Murphy AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Murphy home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Murphy AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Murphy AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Murphy families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Murphy, TX
Our Reviews by City
Michael S. completed annual heating tune up.
Tested all components all measured within ratings and specs. Refrigerant level is normal. Washed and cleaned condenser. Customer changed filter recently. Drain backed up recommended clearing and treating.
Upon arrival system was in working condition. Looking at the indoor unit all electrical connections and components are good. Blower and coil are clean. Drain lines had build up , cleared it. Recommended drain pan strip. Filter is clean. Uv bulb is out , recommended bulb replacement or uv upgrade. Heating components and safetys are good. Looking at the outdoor unit all electrical connections and components are good. Capacitor within tolerance. Amp draws are acceptable. Cleaned unit inside out. Opened up louvers of return grills because it was making noise. Customer is not happy with how much her electrical bills are coming out to be with this new system. Will talk with supervisor to see what we can do about it. Left system in working condition.
Tech arrived for a 2016 2 system Armstrong Air system tune-ups. Upon inspection 3 of the 4 capacitors were out of tolerance. The contactors were in working condition. The condenser coils were dirty and were hosed off to assist with air flow across the coils. There was no observed surge protection. The filters were relatively clean. The drain systems were clear and bleach was poured. There were no drain safeties on the systems. The Deltas were within range. The customer was informed of recommendations today. The customer will budget for repairs in the future and will consider becoming a member at that time. The systems were functioning upon departure.
10 year old Goodman gas system, system is operating normally at this time.
Compressor locked out, restarted and house start heating real good.
Level 2 duct cleaning 1/2 price special
Upon arrival found system satisfied at thermostat. Turned on heat to test furnace. Found clean combustion at the furnace. All safeties were working properly, igniter and flame sensor look good and do not require maintenance at this time. Blower motor was working properly and blower capacitor was within manufacturer specs. Blower wheel was very dirty and duck work was very dirty as well. I recommended to the customer about getting a duck cleaning since they haven't had one before covid and customer agreed to have a level two duct cleaning done. I explained to the customer that this would help with system health and air quality. Treated customers drain line with bleach provided by the customer. Air filter was changed recently and customer will wait till after a duct cleaning before changing the filter again. Found no other issues with the system.
5 year old Lennox gas system, system is operating normally at this time. Duct cleaning.
Arrived for water leak call Secondary drain line dripping in backyard Primary drain line backed up - blew out and treated with pan strip
Sold LV 4 HP 60k horizontal add new supply to upstairs bathroom
Completed evaluation. System not running on arrival. System had multiple shorts. Attempted to run new wiring to units but still couldn't get unit to turn on. Made appointment with advisor Sunday 10-12
Super tune up due to no cool Dual run cap showing 0 for the fan. Fan not operating. Replace dual run cap. Fan and compressor both running hot but functional. Indoor unit is impeccable.