The purpose of your heating, air conditioning, and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the air quality and circulation of your home to help fight against respiratory and other illness. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your North Richland Hills home? If you answer “no” to this question it is time to have your unit inspected.
Comfort Experts, Inc. has made it our mission to keep North Richland Hills families comfortable all year long and assure that your home is a safe environment. No matter the issue of your North Richland Hills AC, we can help you. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to correct function. We will even pay up to $99.00 for you to have a second North Richland Hills AC Repair company come out and inspect your unit before we do the work. By offering to pay for a second inspection, you know that we will pay close attention to detail in order to guarantee we have accurately diagnosed any issue.
If your unit is unable to be repaired and has to be replaced, we are able to replace and install a new unit for you, with very little effort from you. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your North Richland Hills AC needs. Once you have chosen your new unit, we will install it for you quickly and without error so that you can live comfortably again.
Our four-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work that we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your North Richland Hills AC repair needs.
North Richland Hills and neighboring cities are being served through our Fort Worth AC repair location. If you know that you are in need of North Richland Hills AC repair or are just looking to have your unit inspected and maintained, please call our Fort Worth AC repair location by dialing 817-587-8859. You can also visit us on-site at 5001 S Hulen St, Fort Worth, TX 76132. Schedule an inspection today and see why we are a leading company in North Richland Hills AC repair!
Zak was very knowledgeable and experienced. He did our tune up in a decent amount of time as well as fixed our digital thermostat that’s been having issues.
The young man was very professional, wore shoe covers, was very through. Took pictures and explained his findings. He was a pleasure to have dealt with to service our ac unit for its semi annual clean and check
Jordan B is awesome! Shows up and gets the job done. Tells you everything up front and let's you know what the cost is. Jordan is an asset to your company!
Relieved to have the comfortable home with the air and heat guaranteed by the Comfort people. Good job!
Very good explanation of my situation and options.
He was very nice and very thorough.
Would refer to family and friends
Promp services, expertly done and highly dependable.
Response from Comfort Experts Inc.:
Thank you, Joseph, for trusting us to get the job done. Your 5-star review and gratitude mean a lot to us!
Casey Dobbs was above board in his knowledge, customer service and work ethic…don’t know if I ever met a more I formed air tech…truly a credit to his company!
Response from Comfort Experts Inc.:
Thank you for having us out to repair your ac, we appreciate the feedback!
Arrived for STU x 2 Upstairs unit Indoor Filter replaced Drains clear Coil and blower clean of bio growth corrosion and dust Outdoor Cap in tolerance Coil washed Charge good amp draws fine Downstairs unit Thermostat constantly resetting - pulled from the wall and hard reset - working now Drains clear Filter clear Coil clean Blower a little dusty Outdoor unit Amp draws fine Variable speed communicating system Coil washed Charge us good
Performed ac. System operation normal, refrigerant levels in range, capacitor in tolerance, compressor elevated amps, coil is severely rusted and corroded, primary drain line is clogged, customer declined repair and it going to take care of it themselves
Arrived for CTU system functional Indoor Filter replaced Drain clear A little dust on blower Bio growth visible - UV system installed Outdoor Cap in tolerance HSK installed Coul backwashed Amp draws good Charge good
Upon arrival found system running but not cooling efficiently. I evaluated the indoor unit and found new air filter and delta at 10. Blower was working appropriately. Drain line was clear. I evaluated the outdoor unit and found refigerant levels to be low. Performed leak test and found leak on vapor line on indoor unit coil transfer from copper to aluminum. Also txv is bad and not working properly. System is keeping house at about 80 degrees. Submitting for parts.
Arrived server room noise, compressor amps pulling 17 system in poor shape could fail
Arrived for STU NC Compressor not on - outdoor cap 70/5 rated 0/4.5 tested - replaced Outdoor Coil washed Charge a little low - declined fill Cap replaced Amp draws fine Indoor Filter good Cap good Drains clear Could not access coil compartment due to mounting strap on the door No dust on blower
System low on refrigerant, conducted leak search and could not find any sign of a leak, I added 23oz of refrigerant to get charge right and need to return in a week or two to check if perhaps I just didnâ€™t charge the system correctly the last time I was here or if there is a leak
Did a CTU on system, checked capacitor, changed filters,flushed drains, recommended a compressor saver,refrigerant levels are good, customer verified unit was working properly when leaving,customer stated wants Joel B or Mark Grant to come back for next visit
Sold (2) LV 1 42k gas horizontal system with new disconnects, whips, drain pans, safety switches and level 2 filtrations
Low refrigerant, leak on lineset going to evaporator coil. System upgrade do to age condition and refrigerant phase out.