Comfort Experts promises customer service that exceeds the expectations of Poolville, TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Poolville TX.
Hobson AC/Comfort Experts service exceeded my expectations and believe me with Hobson being my last name we are our biggest critics. Brian, Brady, Joe, Jose, Daniel and Jonathan all showed up and within 3 hours had the new Generac generator set, hooked up and professionally installed. I could not be any more pleased. I’m not looking forward to another electricity outage but if we have one we are a little better prepared. Thank you gentlemen on a job well done. Mr. & Mrs. Hobson Peaster, TX.
Shiwed uo on time and git the jib done
The technician was very helpful and explained everything and told me what I needed to do the next time it happened
Great job guys. Think about this who needs their AC fixed on December 27th. We did. Great job.
He was very professional and told me options that I might have to do
Response from Comfort Experts Inc.:
Thank you for taking the time to provide the awesome feedback Karen!
The three men that came out did such a great job I was so amazed how will they did considering the conditions they were working with in such Heat I feel so bad for them but overall I couldn't have asked for a better crew
everyone is so nice weather its the office or worker
12-7-22 Phase 1 complete.
Performed ah, 8 year old dual fuel propane Lennox, system operation is normal, high dust levels in return, dual run capacitor is testing out of tolerance and will cause failure in future if not replaced, cleaned condenser of leaves, customer has no water to wash system.
Thermostat wires incorrectly, fixed wire and heat strips were active
Heat strips not coming on due to wire to contacactir being incorrectly placed, common wire was on top of the contactor and not on low voltage side, placed wire in correct spot and system operation is normal
Wire coming from meter is to small from the panel
Tech arrived to house not cooling. Discovered condenser fan was not working. Checked voltage, contactor and capacitor and found they were all good. Ohm tested the fan motor to discover it was bad. Replaced fan motor and 70/5 capacitor. Unit was running when tech left.
Fix well house put in filter and fix drain in main bathroom
Amana heat pump and air handler installed in 2020. Ecm blower and coil are clean. All electrical connections are tight. Heat strips are in range. UV bulb is original to the install and needs replacement. Filter is clean. 35/5 dual run capacitor is good. Multi speed fan motor is good. Outdoor coil is clean. Air flow and refrigerant levels are satisfactory.
Need to bring three-quarter PVC fittings 1 inch PVC fittings and some half and three-quarter see PVC fittings when I come back to fix the well house
Install 30k hp horizontal cut in with duct system