When you live in White Settlement, your air conditioning unit is crucial to the comfort of your home. Whether the day is just blistering hot or you are entertaining a group of people in your kitchen, the temperature of your home is important. When you are in need of AC repair in White Settlement, then look no further than the reliable team at Comfort Experts, Inc.
When you need White Settlement AC repair, a heating repair, or help properly maintaining your unit and making your home more energy efficient, then don’t hesitate to give us a call.
We are experienced in AC and heater repair and offer you a complimentary estimate when you call us. We don’t want you to have to open your wallet until the services are complete. We thoroughly explain the issues that your unit is facing so that you can decide if you would like to get a second opinion or if you want us to proceed with the AC or heating repair. Our AC service in White Settlement, TX is the location we work out of to provide you with the best experience possible.
We go beyond typical repairs and offer services that can actually help maintain your unit so that it performs properly in the years to come. We understand that heating and AC repairs in White Settlement need to be done in a prompt and professional manner. We offer you a one hundred percent satisfaction guarantee because we are confident in the work we provide you with.
While we are best known for our quality AC & heating repair, maintenance, and installation services in White Settlement, we also offer you additional services to ensure that you have the proper air quality and energy efficiency in your home. These services will save you money down the road and protect you from harmful elements in the air.
We check the attic for leaks where air may be getting in and out and make sure your entire attic is effectively insulated. The ventilation of your home will also be checked. One common problem people make when getting an AC unit installed is getting the wrong size for their home. We make sure that you have the right size unit based on the square footage of your house.
We check the vents to ensure you have the proper amount of them and then turn our attention to the return to make sure it is in its appropriate place. Drafts around doors and windows can cost you a lot of money on AC repair in White Settlement because they allow heat and cool air to escape. We inspect those trouble spots where drafts are most likely to occur.
Contact us today in White Settlement, TX by calling (817) 341-5149 or using our online form to schedule your service.
Serviced both units and advised on necessary actions on future servicing.
Easy scheduling, arrived as promised work completed on time.
Casey was knowledgeable and was very friendly and very professional.
He was not qualified to give the quote we needed. but he did a good job showing what he found and scheduling an engineer to give us a quote.
Went to house for heating and cooling check up on two electric systems. Checked indoor units in heating, downstairs unit first. Changed filter, temperature rise/fall is good, electrical connections stable, drain lines clear. No water safeties, recommended drain switch. Evaporator coil looks good, heat strips are functional,blower is clean, ducts are clean. Checked indoor upstairs unit, filter clean, ducts clean, biological growth starting in system near blower and in blower, recommended uv system. Drain lines are clear, no water safeties, recommend drain switch on this unit as well. Electrical connections are tight, evaporator coil is clean. Temperature rise/fall is good, went to outdoor condensor units and checked them in cooling. Checked upstairs condensor unit first, fan amps draw good, capacitor in tolerance, compressor running fine, condensor coil is clean, defrost board burned in one spot, recommended replacement. Checked downstairs condensor unit, fan amps fine, compressor amps
3/23/23 Upon arrival found system heating and cooling. Capacitor was low and was changed under P&L warranty. Coil was clean. Filter was dirty and was changed. Customer renewed copper membership and system was left heating and cooling with a 20 delta.
Went to house for super tune up on one full electric system. Checked indoor unit in heating, filter is clean, ducts are dusty, recommended duct cleaning, blower is clean, electrical connections are stable. Drain lines and drain pan are clear, no water safeties, recommended drain switch and wet switch. Biological growth starting to form inside indoor unit, recommended uv system. Insulation looks good, ducts are sealed, unit is operational in heating, went to outdoor condensor unit and checked in cooling. Fan amps are fine, compressor amps are good, cleaned condensor coil, coil clean, defrost board is working, recommend replacement as defrost board has burn spots. The system is operating well in heating and cooling.
On arrival customer expressed that the system would not heat when it got cold out, upon further investigation found the the system was a 3 heat 2 cool and the thermostat was a 1 heat 1 cool and would not call for aux heat to turn on. 2008 Goodman Air Handler Evaporator coil was acceptable Blower motor was acceptable Blower wheel needs to be cleaned Drain pan drain has rust needs a new drain pan Heating elements were functional and within manufacturer range Changed the filter for customer Drain was clear and draining poured a gallon of water 2021 Amana Heat Pump Electrical connections were acceptable Refrigerant levels were acceptable at this time Fan blades and motor were acceptable Dual Capacitor was within manufacturer range Washed the unit from inside out Waxed the top of the unit Condenser coil was acceptable Cleaned the blower wheel, installed the drain pan treatment , installed the proper thermostat for customer , ordered drain pan and will be back to instal the drain p
Arrived for STU #solar 1 year old Goodman furnace bio growth already starting to form on the drain pan - UV system recommended to eliminate and prevent spread Drain switch recommended for the primary drain line Insulation recommended to cut utility bills in half Currently using a merv 2 filter. Recommended upgrading filter to prevent dust build up on the system
3/1/23 upon arrival found system heating and cooling with a 20 dt. Tested capacitor and found that it was reading lower than it was rated for. 45/5 reading 42.5/4.5. Replaced capacitor under p&l warranty. System's drains are clear. Filter was dirty and needed to be replaced. Customer is waiting to receive it from amazon and is going to change it themselves or next time we come out. System was left working with a 20dt
I fixed the air flow position on the mini split system and cleared filter . Customers understands that filter in mini split needs to be changed. Out side condensor is clean and clear. Looking at primary goodman furnace and installed second uv light at the return/ blower Water heater is being serviced by another company. Customer has solar installed.
Reattached wire that customer dog chewed, customer is not home but gave me permission to go in the back yard. Let dispatch know that I can’t guarantee that the system is working now since I can’t get inside but the damage is fixed, also customer needs to pay service fee
9 year old Goodman heat pump, system is operating normally at this time.
Customer is pastor of a church. His residence is the parsonage. He has a 42k system and the church requires he get additional bids and approval from the board before we can get a contract. The church is closed until next week putting him into the new year with the new pricing I currently don’t have. I did not quote him today but will email him the quote next week when we get the new pricing.
Call (817) 341-5149 or Message