Everman AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Everman home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Everman AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Everman AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Everman families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Everman, TX
Our Reviews by City
Tim - Everman, TX 76140
Gabriel - Everman, TX 76140
I had my air/heat until
Jacqueline - Everman, TX 76140
Marshall G Review
Iris - Everman, TX 76140
Marshall G. My technician wonderful! Very knowledgeable and did everything in his power to restore the a/c.
Arlan - Everman, TX 76140
Fast, Great, and Detailed Service
Dylan - Everman, TX 76140
We were really Impressed with Casey
Donell - Everman, TX 76140
Heating Tune Up
During inspection verified that system was working properly Customer showede that the vents that had build up on them was the return vents and I let her know that it is caused from sucking everything in the room in so that it's not coming from the system itself Gave customer a recommendation list of some accessories that would help the system and customer denied service saying that she could not do it at the current moment
Ran HTU on unit. All components tested good and drain line was clear. Recommended installing a compressor saver along with replacement of UV Bulb. Found no other issues at this time.
HTU complete. Customer is aware the need of an upgraded system. Customer expressed Financials and that they tried getting approved with us earlier this year but couldn't. Customer is looking to use her Home Depot card (verified card can only be used at home depot) to get system replaced and was expressing her apologies for not being able to use us for install. Customer called home depot while i was there and I helped relay the information to the home depot representative.
Outdoor unit is operating, refrigerant levels are good at thistime, coil is severely dirty recommended deep clean,indoor unit is operating, drain line is clear at this time, heavy biological growth is on indoor unit, recommending uv system and duct cleaning ,performed deep clean on outdoor unit, left system cooling
Tyler L completed electrical etu looking at her main panel it has some burn damage on the right bar not currently in use she was telling me about how she had a fire and how she had also gotten that anal placed before I checked voltage and Titan connections on all of the breakers I checked plugs inside of the house and make sure GFC eyes are present and functioning I recommended to her a surge protector and I have emailed that estimate to her
Upon arrival system was in working condition. Looking at the indoor unit all electrical connections and components are good. Blower and coil are clean. drain lines are clear and flowing. Filter was changed. Looking at the outdoor unit all electrical connections and components are good. Capacitor is within tolerance. Refrigerant levels and amp draws are acceptable. Cleaned unit inside out. Client is interested in a compressor saver but wants to wait 2 weeks to buy. Requested me to come out and install. Left system in working condition. Thank you for choosing comfort experts.
Arrived at location and spoke with home owner. Home owner indicated that indoor unit was not functioning. Inspected indoor unit. Electrical connections tight. Appropriate voltage at all terminals. Blower motor faulty. Recommended blower wheel replacement. Discussed time frame to aquire motor and cost. Recommended appointment with Comfort Advisor for system replacement due to cost and possible time frame for replacement of just the blower motor.
Upon arrival to customers house system was cooling Air handler Blower wheel clean EVAP coil clean Electrical connections good Drain line clear Drain switch working Filter changed Straight electric condenser Contactor good Coil clean Compressor good Fan motor good Electrical connections good Cap was below tolerance, talked to customer about it and she said she would need to hold off until July for when she got paid and then have us back out to replace it Went ahead and got her onto the copper membership so we could keep up with maintenance and get her the 20% off of capacitor Customer said she would call back in July but would still like the office to call her Incase she forgets. Left customers house with system cooling
Upon arrival to customers house system was cooling Air handler Blower wheel clean EVAP coil clean Electrical connections good Drain line clean Filter clean Straight electric condenser Contactor good Cap within tolerance Coil clean Compressor good Fan motor good Left customers house with system cooling
Replaced primary electrical control provided by client
Arrived to no cool. Discovered unit not calling. Checked 3 amp fuse to tind it was intact. Tested transformer to find 240 bolts coming in and 0 bolts coming out. Changed transformer and system started up. System running in cool with 15 degree delta T upon departure.
Insect below contacts on primary electrical control, got cleared system is operating at this time.
05/17/23 Tyler L completed etu Customer would like to do the estimated work, needs a credit app and would like this too be ran Monday 22nd of May
Arrived at location and spoke with home owner. Inspected indoor unit. Electrical connections tight. Blower wheel clean. Coil clean and in good condition. Temperature delta within acceptable range. Inspected outdoor unit. Electrical connections tight. Capacitor in spec. Fan and compressor Amp draw good. Refrigerant charge good. Coil in good condition. Discussed membership options, benefits, and cost savings.
Arrived on site greeted cx thanked them for business. Cx said their condenser was not coming on since the storm came through last night. Checked breaker box to see if it was tripped that was not the case. Went outside hooked up gauges to test low pressure standing was 100 psi no low pressure fault. Checked contactor for continuity checks out. Checked disconnect from line 2 line for 240v 120v was the reading initially thought it was the disconnect swapped disconnect still only 120v. Checked breakers for voltage no reading. Cx went to buy new breakers 2 single 30 amps I replaced still 120 volts. Upon going back to the breaker panel the new breakers I just replaced were not working. I believe the issue lies within the panel itself told cx that we would refer electrical. Service to electrical for Monday the 8th.
Arrived on site greeted cx thanked them for business. Moved to outdoor unit cx advised that this is the 3rd condenser that has been installed since they have owned the home. Data tag has been removed completely. Tested all components fan motor is pulling 1.2 run amps compressor 6.7 run amps dual run cap is within ratings. Primary electrical control was satisfactory. Refrigerant level is low sat temp was 10 degrees with a superheat of 52 degrees with a piston metering device. Washed and cleaned condenser. Moved to indoor 25 year old unit tested all components all measured within ratings. Blower wheel has a massive buildup recommend cleaning coil also has buildup also recommended cleaning. A leak test on the coil was performed leak was not found the restrictions on the system may be cause for low readings and removing those restrictions a good reading could not be achieved is what I advised the cx. Filter was just changed by the cx before my arrival. Drain is clear at this time. I advise
2008 Amana heat pump with air handler. All electrical connections are tight with no corrosion. Heat strips are in range. Evap coil is clean but blower wheel is slightly dirty. PSC blower motor with 15mfd capacitor are acceptable. Delta T is in range, airflow is in range, but refrigerant levels are low. Could not locate leak. Dual run capacitor and contactor are acceptable. Condenser fan motor is making a loud noise and there is some shaft movement indicating worn bearings. Compressor is acceptable. Customer is interested in Germicidal UV System.
Determined water heater busted at base and soaking walls creating deterioration. Stated needs to see if insurance will cover
Dual run capacitor, primary electrical control, build up on blower wheel, duct cleaning, furnace is falling apart, evaporator coil rusty and corroded, system upgrade do to age condition and refrigerate phase out. Replaced dual run capacitor under lifetime warranty.
Arrived at location and spoke with home owner. Inspected indoor unit. Unit clean. No rust. Minimal dust. Blower and coil in good condition and clean. Electrical connections tight. Changed filter. Drain clean and clear with wet switch in place and active. Temperature delta in acceptable range. Blower capacitor in spec. Inspected outdoor unit. Refrigerant pressures good. Coil clean and in good condition. Washed coil. Fan and compressor Amp draw good. Capacitor in spec. Electrical connections tight. Recommended surge protection, compressor saver, drain pan strip, and UV light system.
Arrived for AHC #IAQ ‘15 Rheem Heat Pump No water safeties present Tons of biological growth contamination - on the coil and blower Heat strips are fine Washed the condenser coil Capacitor in tolerance Running Amp draws fine Hard start recommended due to high starting amps on compressor
Inducer motor, inducer housing rusting, furnace is coming apart. Evaporator coil rustyband corroded, system upgrade do to age condition and refrigerate phase out.
Install heat pump 48k upflow, disconnect, whip, new supply plenum and duct cleaning
Performed a heating tune up. Compressor and fan amps within specs, contactor burned, dual run capacitor is below specs 40/7.2—45/10mfd, evaporator coil rusted and there is a substantial amount of biological growth inside the air handler. Customer will have her home warranty take care of the capacitor. Recommended a UV as well.