Pantego AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Pantego home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Pantego AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Pantego AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Pantego families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Pantego, TX
Our Reviews by City
Upon arrival for service system on and not cooling. Inspected system and found capacitor out of tolerance. Replaced capacitor. System came on and cooled properly. Recommended compressor saver kit to help reduce wear on compressor and capacitor. Left system on and cooling.
9 month old trane. System operation is normal, drains clear, changed filter. Ducts are extremely dirty, will decrease lifespan of brand new system if not cleaned or replaced.
Completed ETU Panel looks good but has double lugged neutrals Gfcis needed for kitchen and 2 baths Cover plants needed on 2 outlets And need a tandem breaker too put in any surge protection Said she didn't wanna do anything today due to her car getting serviced
Tech arrived for a Parts and Labor Warranty HTU. Upon inspection, the capacitor was within specs. The contactor was in working condition. The condenser coils were dirty and were hosed off. The system did not appear to have Surge Protection. The filter was dirty and replaced. The drain system was clear and bleach was poured. There was no pan treatment strip. There was no inline drain safety switch however there was a wet switch. The UV system was functioning. The UV bulb has been in the system since installation. The older the bulbs are, the less effective they can be. The customer decided to replace the UV bulb today. Customer was informed of recommendations today and she would like to wait on the Surge Protector until her next visit. The customer is aware that we provide Solar and does not wish to recieve additional information at this time. The system was functioning upon departure.
Customer had his thermostat break during the storm so I could not perform a proper tune up. A Honeywell thermostat was offered but they wanted to go with another nest thermostat. Customer is going to go purchase one from the hardware store and then reschedule the tune-up and a thermostat install in the near future. Job is being paused until then.
Completed tune up. Outdoor unit capacitor in tolerance. Fan and compressor pulling normal amps. Refrigerant level ok. Washed outdoor coil. Indoor unit blower wheel clean. Filter clean. Drain clear. Coil has no corrosion. Uv bulb working. Recommended compressor saver to extend system lifespan. System running in cooling on departure
Arrived for NC/leak call Outdoor Slightly low on refrigerant Cap in tolerance Indoor VERY corroded Unit is leaking directly into the secondary drain pan Water came out of several screw holes once screws were removed secondary drain pan is also very corroded Drain lines are clear Customer has to talk to a banker about financing due to several upgrades she recently purchased for the home