Comfort Experts promises customer service that exceeds the expectations of Richland Hills TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Richland Hills TX.
He was very great about answering our questions.
Zak provided not only the solution to my immediate problem, Identified potential safety issues, and knew what would be best for my financial situation .
Have used Comfort Experts for years, trust their work and service is always top notch.
They are a great company
He is a great representative for your company. I liked the understandable information he presented. As for as pricing, I do not know how other companies would compare.
2/16/23 completed duct cleaning
STU performed today, outdoor unit refrigerant levels are good at this time and the dual run capacitor is testing within manufacturer specifications. Indoor unit filter is clean and the primary drain line is draining a little slow, all ignition components are functioning properly and the inducer motor is pulling proper amperage. Talked to customer about system cleanliness and insulation, customer purchased drain treatment strip and duct cleaning, spoke with him about insulation and while home generators. Scheduled duct cleaning for 2/16/23 and a free energy consultation on 2/20/23 10-12. Balance will be collected for the duct cleaning when the work is performed, also I told the home owner that if he purchased the level 1 duct cleaning that I would pull and disassemble his blower motor for no charge. He would like the blower cleaned after the duct cleaning is performed.
Upon arrival for tune up system on and heating. Inspected outdoor unit. Fan and compressor amp draw within unit specifications. Capacitor within tolerance. Refrigerant pressure good. Defrost board functioning. Inspected indoor unit. Blower and coil have slight dust buildup. Drain line clear. Electrical heating functioning. Changed filter. Left system on and heating.
Did a STU on 2 year old Amana system, checked capacitor found dual run capacitor was weak replaced under P&L WARRANTY, checked filter recommended to replace filter, drain is good,recommended a compressor saver, uv lighting, and replacing water heater, checked flame sensor and ignitor, checked inducer motor, checked pressure switch, checked safety switches, refrigerant levels are good, customer verified unit was working properly when leaving D
Customer reset unit before arrival but left unit off. Turned on unit and it came on and heated. Power cycled unit to attempt to recreate incident. Power cycled with kill switch and through thermostat multiple times. Could not recreate incident. Customer stated thermostat clicked and only the inducer motor came on. Asked customer if temperature of house had lower. Customer said temperature of house was at set temp. Informed customer if issue occurs again to leave it alone so it can be diagnosed properly. Unit fully functional at this time. All amp draws and voltages good. All connections tight and secure. Left unit on and heating.
Upon arrival for service Customer states thermostat is not shutting off unit correctly. Inspected thermostat. Adjusted wires to ensure no unintended connections. Unit turned on and off correctly
Upon arrival found system tripped on locked rotor, measured inrush amp draw and found with compressor saver installed system is pulling over lra. Compressor saver not engaging on startup, replaced compressor saver and system pulled 30 amps below lra.
STU X3 Hunter 11/02/22 Upon arrival found both systems running and cooling I evaluated the indoor down stairs Lennox furnace. Found filter recently changed by customer. Drain lines clear. Blower capacitor was within spec. Blower motor dusty but properly working. Return very dirty recommended level 2 duct cleaning. Coil rusty but working within spec. Electrical connections good. Door switch good. Tested system in heat. Burners clean combustion. Hot surface Ignitor good glow. Pressure switch properly working. Inducer motor working. Flue pipe good. Overall condition good. I evaluated the outdoor Lennox unit. Coils slightly dirty. Capacitor within spec. Contactor good. Disconnect good. Compressor within spec and working. Fan motor running and within spec. Washed outdoor unit and checked refrigerant levels within range I evaluated the indoor down stairs american standard furnace. Found filter recently changed by customer. Drain lines clear. Blower capacitor was within spec. Blower moto
Gas line needs to be replaced has leaks in the line will need 8 foot of 1 inch black pipe 30 foot of 1 inch flexible pipe 4 foot of three-quarter pipe to come down the wall to the gas furnace a new gas flex and gas stop Customer will be calling in today to let me know what he wants to do 10/31/22
Thoroughly performed a heating and cooling tune up, washed condenser coil and checked components. Outside unit was replace this year with a 2018 condenser, furnace is still functioning but doesn’t have a sediment trap, drain line is taped together and clogged at sewage line, customer said he will take care of all drain issues himself and the evaporator coil is extremely rusted up. Spoke with customer about system upgrading to something reliable and more efficient.
Call (817) 341-5149 or Message