Comfort Experts promises customer service that exceeds the expectations of Strawn TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Strawn TX.
Great service. Needed Fall service of unit. Tech was dispatched and got it done. Filter was shipped out ahead; was installed and heating unit tested. Tech showed owner how to activate emergency heating. Have used this company since 1978 in 3 different houses.
Response from Comfort Experts Inc.:
John, thank you for sharing your gratitude and appreciation with us! We're very grateful for our loyal customers like yourself. Thank you for calling on us time after time!
Tech arrived as scheduled. Unit was not switching to emergency heat. Tech adjusted unit to start heat cycle. My household of young cat and my self really appreciated the help.
STU performed today, outdoor unit refrigerant levels are good at this time and the dual run capacitor is testing within manufacturer specifications, I cleaned the condenser coil with a water hose, indoor unit filter is clean and the primary drain line is clear, defrost cycle is functioning properly and the system is working as it should in both heating and cooling
Unit working as should.
Drain line became unglued further down drain line in house causing second leak. Glued drain back together and also checked out mini splits. Vacuumed out both drain lines, no leaks spotted after drain line vacuumed out. All units running on departure and working properly, no leaks spotted in drain lines.
Performed a water leak. Unit is cooling, customer said the problem was a water leak. Glue on pvc was old and pvc had a crack on it. Replaced p trap under warranty and no leaks detected, took pictures of water damage and left unit running in cooling. Customer would like a mailed invoice
Performed a no heat inspection. 2 year old amana split system heat pump combo. Upon further investigation the thermostat was calling for heat and the board was not sending the signal. Used cool loud to reset board and customers heat strips were coming on and drawing amps within range. Left system on 75 heating was 73 when I left
Heating and cooling tune up on Goodman high-efficiency 14 sear heat pump system in Strawn, TX 76475. Replaced filter media and condenser fan motor under warranty.
Heating and cooling tune up on nine-year-old Goodman high-efficiency heat pump system in Strawn, TX 76475. Refrigerant leaks detected on evaporator coil verified system low on refrigerant.
Heating and cooling tune up on Fujitsu mini split to head system Instron, TX 76475.
Annual heating and cooling tune up on a 5 year old Goodman AC
Annual heating and cooling tune up on a 10 year old Amana heat pump.