Comfort Experts promises customer service that exceeds the expectations of Trophy Club, TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Trophy Club TX.
Joe and Jose with his team replaced 2 full systems for me. They did it to my 100% satisfaction with professionalism. This is by far the best contractor experience I have had. Before he left he tested everything with me to ensure I was satisfied. I would use comfort experts again for sure.
it was his last call of the day, it had begun to rain, and he had a long drive back home ahead of him. But he cheerfully checked out the system, indoors and out, found a drainage problem that required extra time to fix, eliminated the small gas leak that required service in the first place, and left me two furnaces perfectly tuned and running. Throughout all this he was cheerfully took all the time the work needed. I am grateful to Comfort Experts for hiring such fine people!l
It wasn't mark Bennett who was here; it was Ty, and you should be very pleased to have such an excellent young man on your staff. He is competent, informative, pleasant, and does excellent work. Thanks
Our technician came for our annual inspection. He was extremely polite and listened to every concern. Made sure to address all issues before leaving.
The crew was friendly and efficient. I thought they did a wonderful job.
Panel looked good had the gfi and smoke alarms
Arrived for service eval Unit is disconnected from power Flipped switch and unit came back on The control board has a 15 amp fuse that is allowing too much current - the board is singed in several places front and back and should be replaced before it fails No water safeties on the unit Secondary drain pan is very corroded Cst declined all repairs and will have her home warranty company do the work
Level 1 duct cleaning special
Arrived today to perform two blower wheel cleanings and two drain clearing. Completed both tasks and verified proper operation after reassembling blower motors found no issues with the system. Tasks are completed
10 year old Goodman gas system: duct cleaning, replaced filter provided. System is operating normally at this time. Sold Lvl1 duct cleaning to be done 11-17-22
10/25/22 Upon arrival found system cooling and heating. Tested heating operation and the heat ran perfectly like it should. Replaced filter and checked drains. Recommended UV system, customer declined. Cleaned outdoor coil and checked cooling operation. Pressures were good and air coming out of the vents was 50 degrees. Recommended compressor saver, customer declined. System was left heating and cooling and no further issues found.
Did a evaluation on system, checked capacitor,checked filter, drain is good, found the aluminum pilot tubing broke and was allowing the gas to leak out, have to order aluminum pilot tubing and the ferrel gas fitting A
Upon arrival found both upstairs and downstairs systems running and cooling properly I evaluated these downstairs unit and found air filter to be relatively clean and not need to be changed at this time. Drain line had debris visible inside PVC. Indoor coil also had debris on the coil. Blower motor was working properly and blower housing was dirty. All electrical wiring inside control panel was tight and clean no burn marks or loose wiring was found. Heat pump was working properly. I evaluated the outdoor unit and found refrigerant levels to be within Target range. Outdoor unit control board was in good shape with no Burns visible. Dual capacitor was within manufacturer specs. Outdoor coil was dirty and was washed at the end of the call. I evaluated the upstairs unit indoor unit. Found blower motor to be working properly blower capacitor was also within manufacturer specs. Air filter was dirty and was changed. Indoor coil look good no rest was found. Drain line was clear. Tessa the ind
Apon arrival found systems running and cooling I evaluated the main system for the house and found blower motor working properly blower housing was very dirty recommend a cleaning. drain line had debris air filter needs to be changed customer did not have replacement. tested system in heat and found clean combustion and heat on furnace heat pump was working properly I evaluated the outdoor unit found coils mildly dirty compressor and fan motor working properly refigerant levels within range capacitor was low and changed under P&L contactor looked good washed outdoor coils I evaluated the master bedroom and found blower motor working properly. blower housing slightly dirty drain line had debris in it Air filter was dirty needs to be changed customer did not have one hand. tested system in heat and found clean combustion on furnace heat pump was working properly evaluated the outdoor unit found coils mildly dirty compressor and fan motor working properly refigerant levels within rang
Upon arrival for tune up systems on and cooling. Customer complained about improper drainage. Inspected drain lines. PVC from sink into drain blocking flow from drain lines. Trimmed pipe and cleared drain. Drained properly after testing. Inspected indoor units blowers and coils clean. Downstairs drain switch disabled on arrival. Filters good but installed backwards on upstairs unit. Inspected outdoor units. Fan and compressor amp draw within unit specifications. Capacitors within tolerance. Refrigerator pressures good.