Homeowners in and near Kennedale and Mansfield, TX have trusted Comfort Experts to troubleshoot, diagnose, and repair all of their air conditioning and heating problems for many, many years. Comfort Experts is a well-respected name in Mansfield and Kennedale, TX, and our customers make it all possible. If you live in or near Mansfield, TX and you have a need for any heating or AC repair or maintenance, give Comfort Experts a call today. We’ll get your unit up and running properly in no time, and we’ll do it all with reasonable rates and superb customer service. During the winter we can get your furnace up and running with a quick and easy repair.
If you’ve been a homeowner for some time, you likely know the importance of regular AC maintenance on your Kennedale, TX home. But if you don’t know how vital it is to the health of your AC system, here are a few ways you can benefit from regularly servicing your air conditioner.
Especially in-between seasons, regular AC checks are very necessary and helpful. They help prepare your system for changes in temperature and weather, which we all know are common in Kennedale and Mansfield, TX, and they can help us identify potential problems before they get too big.
In addition to regular AC maintenance, Comfort Experts is happy to perform a variety of large and small AC repair projects on your air conditioner. Whether you’ve experienced a complete system breakdown or you have started noticing some problems with your air conditioner, call Comfort Experts for the best AC repair in Mansfield and Kennedale, TX. Here are some reasons you might need to call us for AC repair.
Comfort Experts can also do complete AC installations, energy efficiency evaluations, and air quality assessments. We want to help make your home as comfortable and efficient as possible, and we will do whatever it takes to make that happen. Call Comfort Experts in Mansfield, TX and Kennedale, TX today to set up your AC maintenance or repair appointment.
It’s important that you go with the experts when it comes to home improvements like gas heater repair in Mansfield. A quality company will provide you with services that save you time and are cost effective, and they’ll make sure you’re a top priority from the estimate until the follow-up. You want to ensure that each component is given attention during the furnace inspection in Mansfield, and our team doesn’t cut any corners. We pay acute attention to detail and use accuracy throughout each step so that you’re left with a furnace service in Mansfield that you deserve.
Don’t trust just anyone to handle your next furnace replacement in Mansfield when you can go with our team that uses premium materials and has extensive training. We show up ready to work and we arrive when we say we will. We’re straightforward about what you can expect from our furnace service in Mansfield, and we always put your safety first and treat your home like we would our own. Making gas furnace repair in Mansfield easy on our customers is just one reason they keep coming back, and we’re proud to continue to service the community and provide you with more information when you need it.
Are you looking for:
Matt and his associate where very understanding, empathetic, and prompt in his service. I highly recommend this company in general! I ended up having to replace my entire system a few weeks before Christmas. Everyone who we have had contact with in this company have been lovely and HONEST! Which is difficult to find these days!
Fast and easy.
Excellent technician performed annual service on heating system informed me of status and condition of unit no problems
Hunter was extremely polite and very thorough!
Mark did a fabulous job with the electrical work. He explained everything to me about my service and answered all the questions I had.
The tech that came to my house told me the coolant in my downstairs ac was almost empty, and it maybe a leak, I knew that it was just filled last year, but I was in a meeting and was distracted at the time of service. He told me that I would need to replace my unit at a cost of about $4 to 7k. I called my home warranty company they came out and found absolutely NOTHING wrong with my system the coolant was fine and NOTHING needed to be replaced. Won't EVER be doing business with tem again!!
Joel Buckingham was awesome, great service, very respectful and professional.
The Tech was friendly and knowledgeable!
My upstairs unit wasn’t working after the time up. Devyn came out with a trainee to figure out the problem. It was a simple fix. They were both very pleasant.
Joel performed the tune up on my air conditioning units. He was very informative about them and was very pleasant.
Install 36k downflow heat pump with standard filtration, slab, disconnect, whip, standard digital thermostat, code kit, straight electric to heat pump
Install Interlock, cable, receptacle for customer owned portable.
12/3/22 Upon arrival found system not heating. Issue is that half the heat strips are grounded out and the thermostat isn't calling for w and g at the same time. It's only calling for w and the blower isn't running. Took the thermostat off the wall and tied r w and g together. It ran the heat strips half-ass and the blower. Customers were interested in replacing the system due to the heat strips not fully heating and they were interested in energy savings with a heat pump system. Set up a comfort advisor between 3-5 with rob goldate.
Arrived and performed ptu. Everything was in working condition.
Upon arrival I checked the indoor downstairs unit for heating functionality and everything worked without issue. Filter had been recently changed so there was no need to change them this visit. Outdoor unit had amp draws well within unit specs and the capacitor was within tolerance. It was a bit dirty but I cleaned it. Left customer in heating with a 20⁰ delta.
Upon arrival for AH tune up systems on. Ladder to attic damaged upon arrival. Inspected furnaces. Upstairs unit not functioning. Secondary installed incorrectly and water getting trapped in secondary. Primary drain lines clear. Removed trapped water from primary. Unit came on and functioned correctly. Inducer motor amp draw good. Blower have dust build up. Recommended higher rated filters. Coils clean. Flame sensors and ignitors clean. Recommended repair of drain line. Customer agreed.
Upon arrival for htu unit on and heating. Inspected indoor unit. Coil clean. Slight dust on blower. UV light dimmer. Drain line clear. Electrical heating functioning with good amp draw. Inspected outdoor unit. Fan and compressor amp draw within unit specifications. Capacitor within tolerance. Refrigerant pressure good. Defrost board functioning. Recommended replacement of UV bulb do to age and dimming of bulb. Customer Declined at this.
Up on arrival there were not anormal noise, run both furnaces working properly.
Arrived for HTUX3 All furnaces functional Inducer motor on 5 year old system using too much electricity to run and will fail soon - declined repairs All systems dusty and ductwork should be cleaned 3 year old furnace with older coil - supply plenum corroded - drain pan does not extend underneath supply plenum - join coming off of the secondary drain pan is cracked - some bio growth in the plenum Cst declined all recommendations at this time - cst was advised plenum and drain pan issues can result in water damage to the ceiling
Upon arrival for tune up systems on and cooling. Main area system strait electric. Bedrooms unit inverter board heat pump. Inspected outdoor units. Capacitors within tolerance. Fan and compressor amp draws within unit specifications. Refrigerant pressures good. Defrost board on bedroom units functioning. Inspected indoor units. Drain lines clear. Electrical coil amp draws good. Blowers have dust buildup. Coils clean. Left units on and heating.