Prosper AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Prosper home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Prosper AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Prosper AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Prosper families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Prosper, TX
Our Reviews by City
Sonny - Prosper, TX 75078
6 hour wait. Promised first call at 10am. Completed minor repair at 4:15pm.
Sudharsan - Prosper, TX 75078
Awesome service and pricing
Reginald - Prosper, TX 75078
Jordan did an excellent job. Very professional and courteous
Sonny - Prosper, TX 75078
Very good job.
R David - Prosper, TX 75078
Main: Condenser fan motor leaking oil, dual run capacitor, drain protection, heat exchanger has thermal spots, duct cleaning, system is operating at this time. Replaced filter provided. Master: condenser fan motor, drain protection, duct cleaning, heat exchanger has thermal spots, system is operating at this time. Upstairs: condenser fan motor, duct cleaning, drain protection. System is operating at this time.
Tech arrived at a 2016 carrier zoned tuneup. Upon inspection, the capacitor was out of tolerance. The contactor was in working condition. The condenser coils were hosed off to assist with air flow across the coils. There was no observed surge protection. The filter was recently replaced. There was no drain safety on the system. There was growth present in the system. The Delta was within range. The customer accompanied the tech through the inspection. The customer was informed ofrecommendations today. The customer will wait until next year for repairs. Customer was informed that the capacitor may not last that long. The customer would like an electrician to evaluate the patio outside outlet. The system was functioning upon departure.
#iaq upon arrival for tune up 9 year old systems on and cooling. Customer states issue with smell coming from system and drain lines. Inspected outdoor units. Fan and compressor amp draws within unit specifications. Capacitors within tolerance. Refrigerant pressure good. Inspected indoor units. Downstairs unit drain lines routed both through primary. Also found paper notebook inside of systems coil. Notebook covered in growth and could be responsible for smell. Blowers clean. Coils have slight corrosion buildup. Recommended repairing drains and installation for drain safteys. Customer agreed. Left system on and cooling.
2 system tune up checked out just fine clean filters correct amp draws. Home owners take very good care of there systems and it shows.
Upon arrival for tune up systems on and heating. Inspected units. Changed filters. Drain lines clear. Blowers slight dust buildup. Coils have slight corrosion build up. Main area furnace ignited and heated properly. Bedrooms furnace gas valve received power for a few seconds before opening. Gas valve appears to be starting to jam. Customer said they would call their home warranty company. Both inducer motor amp draws good. Left units on and heating.
Left two estimates for Tesla charger and for lighting circuit up stairs with moving receptacle.
Tech arrived for a CTU *3. All systems were functioning upon arrival. The downstairs system had a capacitor that was close to being out of tolerance. The amperage was a little high on start up. The master system had a condenser fan motor that showed signs of possible oil loss. The upstairs system also had a capacitor that was barely above tolerance and also had a condenser fan motor that showed signs of possible oil loss. This system had a door switch that was bypassed by use of a wire. This wire was removed. All systems did not appear to have drain/pan overflow protection. All drain systems were checked and clear. All condensers were washed and all systems were functioning upon departure.
Completed evaluation. Found dead dual run capacitor. Replaced capacitor and verified unit operating correctly. System running in cooling on departure
Did a complete and thorough inspection of both indoor and outdoor units. Found a bad capacitor and outdoor blower motor with excessive shaft play. Customer did not want.