Are you a resident of Cedar Hill, Texas or a surrounding area? If so, you know that as summer temperatures rise, it gets increasingly difficult to stay cool. The average summer day in Cedar Hill, Texas is 95 degrees, and temperatures can often feel higher due to the dry air. All Cedar Hill, Texas residents know that having a plan to stay cool is important when summer is on its way.
Take stock of your home before summer approaches and identify the areas in which you need to weatherize your home. Make sure the icemaker is producing ice, the windows have a good seal, and you have curtains covering windows that let in a lot of light. Most importantly, complete your AC repair early, and don’t wait for the heat to strike. Call a technician to perform your AC repair in Cedar Hill, Texas in the spring, when temperatures are still lower than 80 degrees. Cedar Hill, Texas AC repair is your best defense against the summer heat.
Even when your AC repair in Cedar Hill, Texas has been completed and your AC unit is in working order, it can still be difficult to keep your body cool at all times, especially when first coming inside after being out in the heat. Always keep hydrating beverages on hand. Water is the best choice when hydrating but you can always drink iced tea, cold sports drinks, or juice when you want the added flavor.
Keep a few oscillating fans on hand in addition to your ceiling fans. Make sure all of your fans are in good working order. When your Cedar Hill air conditioner has been maintained, the temperature of your home will be cool. Fans are a great addition to the cool air as they help to circulate the air your AC unit is cooling. As the air moves with more force, the temperature of your home begins to feel much cooler, even if it doesn’t actually bring down the temperature via the air conditioning unit.
If you have to cook, try to avoid the hottest part of the day. Your AC unit is already working against the heat of the outdoors, and any extra heat from inside will make it harder to maintain a cool temperature. Cook your meals early in the morning to avoid adding extra heat to the already high temperatures.
Try not to spend long periods of time outside during the hot summer months. If it is necessary to spend time outside, have a plan to cool yourself off quickly when you return inside. Even when your Cedar Hill AC unit is in ideal working order, it will be a few minutes before your body will cool down after the abuse of the scorching summer heat. Try eating a popsicle or enjoying sherbet or a soda float while you sit in the cooler air maintained by your AC unit.
Above any other practice, it is most important to make sure that you always put proper AC repair and maintenance in Cedar Hill, Texas at the top of your to-do list if you want to stay cool. Without a functioning AC unit, there is no tip to helping you effectively beat the high heat of the summer in Cedar Hill.
Mr. Boyd went above and beyond with our service! He showed up at the end of the day with a pleasant smile and a good conversation. He even checked other stuff beyond what my concern was and he worked great with my pets!
Well I can't really say much about the service from today due to not much was done. But I will say, Marshall was my tech. He checked all the vents for me w/his phone. They all showed to be putting out 45 to 46 degree of air. He said that was normal. The noise that I was hearing from the downstairs vent in the kitchen was gone. Unfortunately, there was no noise. But I know what we been hearing. (My father was present but I couldn't get him to verify the noise because he was w/the physical therapist at the time Marshall was here. I told him maybe it was because the heater had just been turned on. But I will and can say, he had a great personality & and was very kind to me! He was well attentive to my concerns. I appreciate his tenacity regarding his job knowledge! I would like to say I'm gonna give him a (AVERAGE RATE) because much wasn't done.
Simon did a great job!
The above young men did a fantastic job cleaning my vents, and installing the new system in my home. They were very patient, courteous, efficient, and professional while working at my home. May thanks for the service they provided.
Response from Comfort Experts Inc.:
Barbara, your kind comments and 5-star rating have made our day! We're glad the install crew was able to provide you with the best of service. We appreciate your time and your business, thank you again for choosing Comfort Experts Inc!
It appears that we did not get two major components in replacing our AC unit. As in the Zoning Board & the Damper. Not sure why those 2 items was not added in the beginning for us to purchase w/the new system, especially since we had to buy a WHOLE new unit. My husband & I are now worried about this situation. Because we definitely are in need of them.
Response from Comfort Experts Inc.:
Hi Wendy, thank you for bringing this to our attention. Our Customer Care team will be in contact with you.
Marshal was knowledgeable and very professional.
Upon arrival system on blowing hot air. Inspected outdoor unit. Capacitor out of tolerance. Replaced capacitor. Unit came on. Fan and compressor amp draw within unit specifications. Refrigerant pressure good. Inspected indoor unit. Blower and coil clean. Drain line clear.
Upon arrival found unit on and cooling. Inspected outside unit. Fan and compressor amp draw withing unit specifications. Capacitor weak on the compressor side. Unit refrigerant pressure good. Inspected inside unit. Filter was dirty. Coil looked good. Slight growth on blower motor cables. Changed filter and cleaned outside unit. Customer changing capacitor themselves.
7/22/22 Upon arrival found unit not cooling. The outside condenser wasn't on because the capacitor had gone out. Replaced the capacitor and the system turned on and ran like a dream. Left system cooling with 18dt and drain lines are clear
Arrived for CTU - outdoor off Indoor Drain clogged - float switch preventing outdoor unit from coming on - blew line clear Filter good Bio growth in blower compartment - UV recommended - declined due to price Dust on blower Outdoor Compressor cap good Fan cap out of tolerance - declined replacement Electricals good Coil washed Charge good
STU performed today, outdoor unit refrigerant levels are good at this time and the dual run capacitor is testing within manufacturer specifications, I cleaned the condenser coil. indoor unit filter is clean and the heat strips are pulling proper amperage at this time
Downstairs: 1 year old Goodman heat pump: system is operating normally at this time upstairs: 1 year old Goodman heat pump system is operating normally at this time. Comfort advisor 7-21-22 10-12
Electrical tune up and inspection. Found neutrals double lugged and no ground rod
Sold LV 2 heat pump 60k upflow with level 2 filtration, disconnect, whip, (2) wifi thermostat, adding zoning upstairs, possible new drain line
Upon arrival found system not cooling, compressor not running. Dual run capacitor testing within tolerance, compressor trying to start, tested resistance of windings on compressor and all three windings showed bad on meghometer. Compressor is seized on the 21 year old r22 system, recommend system replacement, customer needs to speak with his wife.
Main house unit is r-22 unit from 2005. Customer has put refrigerant in every two years. Believe there to be a leak. Advised to talk to comfort advisor about replacing unit