Krugerville AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Krugerville home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Krugerville AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Krugerville AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Krugerville families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Krugerville, TX
Our Reviews by City
Scheduled service check
Derron - Krugerville, TX 76227
Service is quick and thorough. They check all components.
Great service with a smilr
Derron - Krugerville, TX 76227
Zak did a great job of taking care of us. He changed out our filter and advised of our upcoming needs. He made sure we knew about specials the company has going on. He was very friendly and helpful.
Removed and replaced outdoor TXV. Recharged and tested both modes all modes performing optimally.
Customer said air blowing from supply was not hot or even warm for that matter I verified. After investigation outdoor hp was not coming on due to a coresense lockout reset. Attempted to duplicate fault hp is tripping on high head pressure after troubleshooting any and all possibilities narrowed it down to outdoor TXV metering device. High head pressure tripping quickly within 5-7 minutes of operation. Ordering part and will return when warehouse has acquired. Auxiliary heat is operational so they have heat while waiting on part acquisition. Entire balance paid in full.
After arrival I took a look at the water meter and and after ten minutes it went up .25 Again, so I then knocked on the door and began my investigation. I first started off in the bathroom where the issue was last time and i noticed that the homeowner did have the fill valve changed. But after looking at it a little bit more, I noticed that it was having the same problem and leaking out of the rubber hose into the overflow. I readjusted the heights and after that it no longer had the issue of leaking So I then went back to the city meter and then watched it for 15 to 20 minutes and the gallons per minute no longer went up. There's no warranty on today's job because no work was actually done. All I did was readjust the fill valve that the homeownerthat had replaced. If this problem arises once again I recommend getting a new fill valve professionally installed, thank you.
After arrival I knocked multiple times and rang the doorbell with no answer. So after finally speaking with dispatch, I was informed that the tenants left at 11 which was in the middle of my arrival time so they are not on property and there's nobody else here. I looked at the meter and after ten minutes it went up .25 and then after turning off the double check valve it did not change for another ten minutes , but before I left , I checked it again (after 15 minutes) and it did and going up another .25 When I was here last I turned off the whole homes Shut off valve which is in the wall in the garage And they meter stop spinning. I then took a look at the hallway bathroom. And the toilet was constantly running. So I shut off the angle stop and then. I checked the meter once again and it quit moving. So I called and told the landlord , and he said that his tenant would change it for him and that he did not want to move forward with our estimate.
Austin V. completed a heating system diagnosis.
After arrival I met with the tenants and they explained to me the issues they've been having with their water bill and they're unsure the reasoning behind it so they called us out here. They recently changed the flappers and fill valves in both toilets back in the summer and they recently started having issues back in mid november once again. I noticed that this was a newer home that was ran in pex piping, which meant that there was no piping underneath the home to cause a slab leak. So I immediately checked the irrigation line and came across no issues so I then dropped color tablets inside each toilet tank to make sure they were sealed properly and I came across no issues with that. But when I was taking a look at the second toilet I did hear a little bit of hissing so I decided to investigate further and there I noticed that water was still flowing through the rubber pipe even though no one has used the toilet in the past 30 plus minutes. The tenant said that is something that she i
12/16/23 Tyler S- ran camera up cleanouts in front yard but main only shoots towards guest bath and that wasn't clogged. I couldn't run and of my small 25' cables in the sinks or shower drain because clog was farther down near the hall powder room. Toilets had water running under floating floors. Had to pull Toilet because it was the closest access to clog and then reset toilet with new wax ring and bolts.
1 year old Trane heat pump: Compressor saver, filter needs to be replaced. Homeowner not home. System is operating normally at this time.
Upon arrival system was in working condition. Looking at the indoor unit all electrical connections and components are good. Blower and coil are clean. Drain lines are flowing. Recommended a pan strip , went ahead and Installed it. Filter was changed. Looking at the outdoor unit all electrical connections and components are good. Capacitor is within tolerance. Refrigerant levels are acceptable and Amp draws are acceptable. Cleaned unit inside out. Left system in working condition. Thank you for choosing comfort experts.
Arrived for rec work unit surge protector installed Installed unit surge protector System running in cooling at exit
Called customer and they walked out turned disconnect back on. They confirmed that the system turned on and is cooling. Recalled service fee due to technician error, will be back out there for a surge protector install on Wednesday.
Arrived for STU #IAQ - raining 7 year old heat pump - Goodman Installed drain pan treatment Filter is fine Coil and blower clean UV bulb good Installed surge protector on the outdoor disconnect Need to come back and install the surge protector on the air handler - Wednesday is best Capacitor and HSK are fine
11/4/22 completed duct cleaning special
Arrived for filter change Swapped filter Scheduled L1 duct clean for friday 11/4
Upon arrival for tune up system on and cooling. Inspected outdoor unit. Fan and compressor amp draw within unit specifications. Capacitor within tolerance. Refrigerant pressure good. Inspecting indoor unit. Blower and coil clean. Heat functioning properly. Drain line clear. Left unit on and cooling.
Evaluated will return to perform repairs
Tech arrived for a STU. Upon. Inspection, the contactor was within specs. The condenser coils were dirty and were hosed off. The amperages were at acceptable levels. The contactor was scorched. This can indication previous issues with the component. This item was replaced with a functioning contactor. The Delta and refrigerant was at acceptable levels. The drain system was clear and bleach was poured. There was growth present in the blower area. This could be due to the UV light not functioning. The UV light was replaced and the UV system regained functionality. There were areas of the plenum and filter box that were leaking air. These areas were sealed. The system is using a Goodman Gray ductwork. This duct is known to have problems including ripping and separation of the duct jacket. There were separation noticed at the time of inspection. Duct replacement is recommended and can reduce heat/energy loss in the duct system. The attic access was missing insulation. This can also l