Paradise AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Paradise home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Paradise AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Paradise AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Paradise families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Paradise, TX
Our Reviews by City
Jim - Paradise, TX 76073
Professional, courteous, good salesman, felt honest, and straightforward. We will specifically ask for Ian in the future.
James Reeves - Paradise, TX 76073
Very professional, knowledgeable and helpful.
James - Paradise, TX 76073
Very professional and knowledgeable
James - Paradise, TX 76073
Tim - Paradise, TX 76073
Tim - Paradise, TX 76073
2018 trane airhandler Checked and tightened all electrical connections Customer recently changed filter Drain was clear and draining poured a gallon of water down Blower motor and wheel were acceptable Evaporator coil was acceptable Heat strip were functional Uv system was functional 2018 Trane heatpump Dual run capacitor was within manufacturers range Electrical connections were acceptable Refrigerant levels were acceptable at this time Condenser coil was acceptable Fan blades and motor were acceptable Washed coil from inside out Waxed top of unit Recommended compressor saver, declined for now
Lots of biological growth on blower wheel and coil Systems airflow little to none Cust expressed to me that he had extremely high electricity bills Recommended level 2 duct cleaning
Upon arrival for service system on and cooling. Primary drain line clogged. Cleared drain line and tested drain. System running at departure. Noted no drain line saftey on system. Recommended installation of saftey. Left system on and cooling.
Upon arrival for tune up system on and cooling. Inspected indoor unit. Blowers and coils have dust buildup. Drain line clear. Inspected outdoor unit. Fan and compressor amp draw within unit specifications but high. Capacitor within tolerance. Refrigerant pressure good. Recommended cleaning of system. Left system on and cooling.
Need to tunnel under home to fix brake under home. It's about 20 ft from outside wall. To break. Could be a little farther then the 20 ft will not know the full price or how much will have to be fix until we get it uncovered Will need to call customer Wednesday 6/7/23 at 7pm to see how we want to proceed
Completed 49 AHC tuneup on 2019 Payne 3 Ton electric heat cool only Electric heating working ok. Heat strip amps ok. Electrical connections ok. No obvious issues. Indoor blower and cap ok. With in manufacture specs. Indoor coil clean with minimal growth or dirtiness. No major blockage. Indoor coil drain pan needs attention. Recommend to customer cleaning and eliminating biological growth in primary drain pan to prevent further issues. Customer will address issue. Drain passed 1 gallon of water with no blockage. Indoor unit working ok. Outdoor unit had an audible sound issue. Further inspection showed the duel run capacitor was no longer working on fan side and out of tolerance on the herm side. I made the customer aware of the issue and the capacitor was replaced. The audible issue was gone after replacement. Comp amps, fan amps, cap, and fan motor with in tolerance. Thermostat wire will need replacing in the future do to wear and tear of outdoor elements. Refrigerant levels ok. 21 d
Excavation and repair successful Added extra charge for concrete chipping during Excavation process. Collected final invoice
Upon arriving smell wasn't present after running water for about 5 minutes strong odor came out, I sold a camera run to see what can be found bur nothing concerning was found in main line, I ran camera in vent pipe clean out located in exterior wall, and found that there was a large gap in the vent pipe and pipe was offset, she stated she's had foundation issues before and new cracks appeared in wall which was why she suspected pipe may be broken. After running camera determined vent detached need tunnel to fix customer paid half
When I arrived customer expressed that the thermostat was loose on the wall and moving around making it difficult to adjust the temperature, after further investigation there was no screws holding the thermostat in place. Customer also expressed that the new system has made the house noisier , explained we can take the metal duct out where each of the vents are and inserts piece of flex duct to reduce the noise. 2022 Amana Air Handler Evaporator coil was acceptable Changed the filter for customer Blower motor and wheel were acceptable Delta T was acceptable Drain was clear and draining poured a gallon of water down UV system was functional Electrical connections were acceptable Fixed the thermostat that was not properly installed 2022 Amana Heat Pump Dual Capacitor was within manufacturer range Electrical connections were acceptable Refrigerant levels were acceptable at this time Washed the unit from inside out Waxed the top of the unit Cleaned debris out of the unit Fan blades
2019 Goodman Air Handler Cleaned some insulation from inside the Evaporator coil Drain was clear and draining poured a gallon of water down UV system was turned off on arrival , turned it back on Heating elements were functional and within manufacturer range Blower motor and wheel were acceptable Changed the filter for customer Electrical connections were acceptable 2019 Amana Heat Pump Dual Capacitor was within the manufacturer range Refrigerant levels were acceptable at this time Electrical connections were acceptable Fan blades and motor were acceptable Washed the unit from inside out Waxed the top of the unit Recommend the customer cut back the bushes around condenser Condenser coil was acceptable Need to order bulb Model# RM2-12/5 Serial # 0031919-SHS1Bc-1598
Goodman heat pump with air handler installed in 2020. All electrical connections are tight with no corrosion. Heat strips are in range. PSC blower motor and capacitor are acceptable. Blower wheel and evap coil are clean. 45/5 dual run capacitor and contactor are acceptable. Compressor and condenser fan motor are acceptable. Refrigerant and air flow are acceptable.
Found communicating thermostat failed, re wires system into legacy mode, and installed new thermostat, system operation is normal in heating and cooling.
Safety disconnect was out, put it back in and the system is functioning properly.
Found primary drainline clogged, disassembled and cleared drain line under the sink.
Gave a cost got a sub panel
5 ton Heat pump and air handler from 2018. All electrical is good. Has UV light that has good bulb. X13 blower that is clean. 70mfd capacitor on outside unit. No fan capacitor. Air flow and refrigerant levels are satisfactory.
Completed evaluation. No issues with the function of the AC unit. Water is coming from a clog in the main house plumbing. Client has had previous issues with same thing and will fix themselves
On arrival found wet switch tripped and thermostat not working properly. Nest will not charge and shuts off when plugged into wall. Installed customer provided thermostat so unit will function while replacement is on order.
Completed evaluation. On arrival unit was operating correctly, although client says it has been shutting off intermittently. Couldn't find anything wrong with it. Outdoor coil was dirty, washed coil. System running in cooling on departure Also collected a check to be dropped at kennedale tomorrow
Modified filter seat, pressed the bottom half down of the filter housing, made a 1inch slit on the top of filter. Fits like a glove
Arrived for STU system operational Outdoor Cap out of tolerance - replaced per PL Coil clean Electrical connections tight charge level good Amp draws fine Indoor filter dirty - replaced Drains clean Small signs of bio growth and dust in blower cabinet No signs of corrosion on coil
60k duct system and level 2 filtration
Copper membership Repairs to replace compressor capacitor with lifetime warranty and clear primary drain line. Adjusting refrigerant levels to spec will be 18.20 an oz. Addition of a drain safety switch to prevent flooding Installed compressor cap. Cleared drain line and installed drain switch. Installed 14 ozs of 410a
Cleaned and inspected system. Located failed compressor capacitor, condenser fan motor, X13 blower motor, improper installation of primary drain line, and holes rusted through duct system under home due to water damage from drain system. Recommend replacement of system over repairs.
Did a AC tune up on 2 units,customer had reusable filters,checked capacitors, flushed drains,refrigerant levels are good, customer verified unit was working properly when leaving