Addison AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Addison home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Addison AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Addison AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Addison families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Addison, TX
Our Reviews by City
William - Addison, TX 75001
Colby is great. A big help.
William - Addison, TX 75001
Colby is great! An asset to the company
Maddi - Addison, TX 75001
Blake was very courteous and professional and explained everything very well.
Will return Friday strong rain and lightening preventing me from adding parts Added the compressor saver kit and the surge protector today, no issues and as I left the system was back cooling. Thanks for choosing comfort experts and have a great day!
On arrival the system was running and cooling and producing a 17 degree delta. The blower and coil were clean and the drain line flowed when flushed. The outdoor unit passed all electrical tests except for the fact that the compressor pulled 138 amps on start up and the maximum it is rated for is 112. I recommended a compressor saver kit to address this and to reduce the wear and workload on the compressor moving forward. Thanks for choosing comfort experts and have a great day!
Tech arrived for a service call. Upon arrival the customer mentioned that there was water leaking in the home. There were water stains in the living room and master bedroom. These areas had temperature differences indicated by the FLIR camera. The tech was unable to confirm proper flashing on the roof and exterior walls. There was a gap in the flashing above the condenser area drain. The area below the condenser is not easily accessible. There did not appear to be any temperature differences below the furnace or water heater. The customer mentioned that they confirmed that plumbing did not appear to be an issue as they turned it off and on to test for leaks. It is strongly advised that the home warranty company/builder be contacted to identify and evaluated damages and sources. The customer would like to be emailed pictures.
Tech arrived for a HTU. Upon inspection the capacitor was within specs. The contactor was scorched. The compressor was pulling high amperage on startup. The system did not appear to have Surge Protection. The filter was relatively clean. The ducts were a little dirty. The drain system was clear and vinegar was poured. There was a pan switch but no float switch. The heating system reached complete ignition. There was water around one of the vents. The area was investigated in the attic and a vent pipe appeared to be leaking as there was water beneath this area. The customer was informed that we provided plumbing services. She is going to try and reach her home warranty company and will call us back out if she can not contact them. The customer plans on getting a duct cleaning done after the construction on the area is finished in a couple of months. The system was functioning upon departure.
Did an evaluation on system found nothing wrong with the unit,capacitor isgood,refrigerant levels are good, superheat is 16 target superheat is 12,subcool is 8.6,temperature drop is 19.4, unit was working properly when leaving, customer wants rob sales manager to call in the morning 06/06/22
5/30/22 Devyn - upon arrival found system not running or cooling. After evaluation system was extremely low on refrigerant. Performed leak test. All field welds were good and warranted no issues. Pulled side panel off at Indoor coil. Near top of coil my leak detector picked up a high volume of Refrigerant. I continued to perform a leak test backtracking to the outdoor coil and found no other leaks. Indoor coil is submitted for parts replacement. Customer agreed it was not necessary to add Refrigerant to the system for temporary cooling as no one will be staying at the house.
Sold LV 3 gas 48k horizontal
Evaporator coil extremely rusty and Corroded, secondary drain pan rusty, duct cleaning, condenser coil has corrosion around bottom of coil, system upgrade do to age and condition.