Lantana AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Lantana home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Lantana AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Lantana AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Lantana families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Lantana, TX
Our Reviews by City
David - Lantana, TX 76226
Allan - Lantana, TX 76226
Homer - Lantana, TX 76226
Tech arrived for rec work. The 210 AprilAire filter upgrade kit and filter was installed and functional today. The system was functioning upon departure.
Tech arrived at a membership tune-up. Upon inspection the filter was dirty and loose in the filter box. This was allowing unfiltered air to move into the blower air. Blower area was dirty. The vinegar was poured down the drain line. The heating system reached complete ignition. The flame sensor was scorched. There was no observed surge protection. The customer was informed of recommendations today. He decided to move forward with ordering the 20*25*4 AprilAire upgrade kit. He will review the other recommendations. We will pause for parts. The system was heating upon departure.
Tested all components all measured within ratings. Refrigerant level is normal. Washed and cleaned condenser. Changed filter.
Upon arrival the indoor and outdoor system was running and cooling. The indoor unit was in good shape factoring in age. The coil was not rusted and the delta of 17 is good. The blower was dusty and it's capicator was out of tolerance. The drain line flowed when flushed but did not have any water safety on the unit. I did advise the customer of the potential for water damage without the safety The outdoor system was fairly clean. The dual run capicator was 29 out of 45 and is likely causing the fan run amps and compressor amps on start up to be above what they are rated. Fan is running at 1.03 and max rated is .93. the compressor is starting up at 128.6 amps and the max is 109. Customer declined to pursue any of my recommendations today. As I left I ensured the system was back up and running. Thanks for choosing comfort experts and have a great day!
Install 36k gas hz use current filtration
Upon arrival system was in working condition. Looking at the indoor unit all electrical connections and components are good. Blower dirty. Plenum is dirty. Recommended a duct clean and uv light but client rejected work. Drain lines are clear and flowing. Filter was changed. Looking at the outdoor unit, all electrical connections and components are good. Compressor capacitor is within tolerance. Fan capacitor out of tolerance but client decided to hold off on that. Refrigerant levels are acceptable. Amp draws are acceptable. Cleaned unit from inside out. Left system in working condition. Thank you for choosing comfort experts.
Arrived for CTU #solar - raining Filter needs be replaced Drain lines are good Blower and coil are clean No surge protection Washed condenser coil Capacitor in tolerance Hard start kit recommended to lower starting amperage to factory safe levels
Upon arrival I checked the indoor unit for heating functionality and everything ran fine. System was very clean. Outdoor unit ran well as well. Capacitor was within tolerance and the amp draws were all within specs. Left customer in cooling with a 20⁰ delta.
Performed ah, system operation is normal, changed filter, removed blower and inspected heat exchangers, found high dust levels in return plenum, flame sensor is highly corroded, supply plenum is damaged from condensation and rusted along with secondary pan. Recommend duct cleaning, flame sensor, drain treatment
Completed 2 system tune up. Both Goodman units installed on Sept. 2020. Downstairs unit: outdoor unit capacitor in tolerance. Fan and compressor pulling normal amps. Refrigerant level good. Washed condenser coil. Indoor unit filter dirty, client did not have replacement on hand. Drain clear. Blower wheel spins freely, no shaft play. Heavy dust level throughout indoor unit. Coil has no corrosion. Upstairs unit: outdoor unit capacitor in tolerance. Fan and compressor pulling normal amps. Refrigerant level good. Washed condenser coil. Indoor unit blower wheel spins freely, no shaft play. Coil has no corrosion. Drain clear. Filter dirty and heavy dust throughout. Highly recommend having duct cleaning performed on both systems to help prevent dust in home as well as wear to motors. Also recommend compressor saver on outdoor units to increase system lifespan. Left estimate for both