Comfort Experts promises customer service that exceeds the expectations of Millsap TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Millsap TX.
Knew what he was doing and was fast and friendly.
Very professional and courteous, took the time to explain things and help me understand!
Very professional and nice young man, and he identified our problem right away.
Andrew did a great job of locating my heating unit’s problem, and then he fixed it. He also track down a couple of other problems that could’ve burn down my house if he hadn’t found it. I’m so pleased with Comfort Air and Andrew!
Ryan did a great job and quickly solved my AC problem.
Courteous and professional.
Very good to deal with
11/30/22 not complete ordering parts will return
Replace contactor. Lennox heat pump with air handler installed in 2019. All electrical connections are tight with no corrosion. Heat strips are in range. X13 blower motor is strong. Blower wheel and evap coil are clean. 70/10 dual run capacitor is good. Contactor was bad, tech replaced it. Condenser fan motor and compressor are good. Refrigerant is slightly low but ate flow is satisfactory.
Sold level 1 duct cleaning to be performed 12/1/22
Move the pump from Barnes bar to trailer spa.
The system won't let me use "Tune up form 1 and Tune up form 2" so I used tune up for 3 and 4 2014 Goodman Air Handler (downstairs) Heating elements were functional and within manufacturer range Drain was clear and draining Evaporator coil was acceptable reccomend cleaning Changed the filter for customer Electrical connections were acceptable No UV bulb in the UV system recommend installing one Blower motor and wheel were acceptable recommend cleaning 2016 Goodman Air Handler (upstairs) Changed the filter for customer Heating elements were functional and within manufacturer range Drain was clear and draining Blower motor and wheel were acceptable Evaporator coil was acceptable UV light was functional but needs to be replaced Electrical Connections were acceptable 2014 Goodman Heat Pump (downstairs) Dual Capacitor was within manufacturer range Washed the unit from inside out Cleaned the debree out of the unit Fan blades and motor were acceptable Primary electrical contactor was
Did a HTU on 4 year old Amana system, checked capacitor, changed filter, flushed drain, recommended a compressor saver, and replacing uv bulb, washed and waxed condenser unit, refrigerant levels are good, customer verified unit was working properly when leaving
Replace control fix Freon leak
Performed a heating tune up, tightened electrical connections and checked heating components. Furnace of operation functioning properly, blower cap is below specs but everything else is fine. Recommended blower cap
Customer is going to buy her a faucet I will come back in and put it in as a discount for the pain she has been having with the other work here.
9 year old Goodman all in one heat pump. All electrical connections are good. Ecm blower motor is good. Evap coil is clean, blower wheel is slightly dirty. 45/10 dual run capacitor and contactor are good. Compressor and fan motor are satisfactory. Air flow and refrigerant levels are satisfactory.