Comfort Experts promises customer service that exceeds the expectations of Millsap TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Millsap TX.
The Tech. Kellen Mullinnex ,was friendly, thorough, & efficient!
Mark Dennison was very friendly and great customer service. Went through detail of what he did as far has making sure everything was in good working shape. Great job Mark!!!
Knew what he was doing and was fast and friendly.
Very professional and courteous, took the time to explain things and help me understand!
Very professional and nice young man, and he identified our problem right away.
Andrew did a great job of locating my heating unit’s problem, and then he fixed it. He also track down a couple of other problems that could’ve burn down my house if he hadn’t found it. I’m so pleased with Comfort Air and Andrew!
Carrier heat pump installed in 2006 with Goodman air handler installed in 2010. Customer complained of odd noises coming from outdoor unit and wanted to get it checked out. Discovered a weak dual run capacitor, a weak blower capacitor, and a condenser fan motor that was leaking oil. Installed both capacitors, a new condenser fan motor, a compressor saver, and re-insulated the vapor line. The first 1/5hp 1085 condenser fan motor was bad out of the box, has a bad start winding. The second motor worked.
Amana heat pump with air handler installed in 2020. All electrical connections are tight with no corrosion. Ecm blower motor is acceptable. Blower wheel and evap coil are clean. Heat strips are in range. Dual run capacitor is in range. Compressor and condenser fan motor are acceptable. Refrigerant levels are satisfactory.
Top restroom Nothing found in the top restroom Drainage works good in sink and supply is strong Toilet flushes and fills normally Shower supply good as well Drains quvk Lower restroom Is okay right side sink has leak on drain and supply is good Shower stops up advised customer of issues found stated has a guy who can take care of it.
Upon arrival found hvac system off. Freon charge was low. Purged line sets and removed shraeder cores. Made sure system was at 0psi then patched the field weld at the suction line. Tested with pressure and soap bubbles and there were no leaks found. Pulled a vacuum for 30 mins and broke the vacuum with 15lbs 10OZ 410. Customer payed flat rate freon fee.
Goodman propane furnace
Found leak at suction line at the condensor were line set welds to the condensor. Please send warranty tech to recoup gas weld suction line and recharge system anytime today works or anytime tomorrow after 2pm
Arrived for a no heat. The OEM defrost board was shorted , UV ballist was shorted as well blowing fuses , thermostat wires were charred and blackened cut them back and re wired the thermostat , 35/5 dual Capacitor was out of manufacturer range replaced that as well. Swapped the defrost board with a universal board , took the UV ballist out of the system ordered a new one under PL , customer purchased a new UV Bulb , told customer to keep an eye on the thermostat it's not malfunctioning while I'm here they are going to keep an eye on it and purchases a new one if it acts up. Also performed a STU Amana Air Handler Drain was clear and draining Changed the filter for customer Evaporator coil was acceptable Blower motor and wheel were acceptable Electrical connections were acceptable Delta T was acceptable Amana Heat Pump Dual Capacitor was out of manufacturer range Electrical connections were acceptable after board was replaced Washed the unit from inside out Waxed the top of the u
Work to be completed first call on 03/03/23, installing a UV light, unit surge protector and a 4 ton compressor saver. Customer is elderly and was tired and politely asked if I could come back and do the work. Called dispatch to inform. CTU complete Drain line clear Filter changed Blower wheel and motor inspected Electrical connectons inspected Evaporator coil inspected DeltaT inspected Outdoor unit washed from the inside out Capacitor inspected Electrical contractor inspected Fan blade and motor inspected Amps and volts inspected.
2/22/23 - Removed spa from trailer removed 4 pipes from the bottom of the spa and sealed fittings to the tanks will be back in the morning to test then we can put it in the building
Call (817) 341-5149 or Message