How well does your Saginaw air conditioning unit perform? Do you feel comfortable when you are at home or does your AC unit require repairs or servicing? Saginaw residents know just who to call when their AC units start acting up. In addition, they also know they can rely on us for AC service in Fort Worth, TX for all their AC needs in Saginaw. We can also help you with the air quality in your home.
If you need Saginaw or Fort Worth AC repair, we can help. Before we even start working, we will give you a free estimate of the cost and the issues that we find. And if you want a second opinion, you don’t have to pay us until after we have completed our AC service call. You can do even more for your AC unit than just getting a service from us. To prevent future Saginaw AC repair service calls, you can sign up for our AC service maintenance agreement to keep your unit maintained regularly. By having regular Saginaw AC service done on your AC unit you can decrease the need for future repairs. Saginaw and Fort Worth residents should be able to use the same unit for as long as they live in the home, provided that the unit is properly maintained. We can provide you with AC service in Saginaw and because we guarantee our work 100%, you have the assurance that you will get your money’s worth. This same guarantee is offered for our heating repairs service. Also, Saginaw and Fort Worth homeowners can depend on us to provide installations and assessments that will enhance the air quality in their homes.
Energy Efficiency and Environmental Quality
We will check your residence for mold, radon, and other hazardous particles in the environment and we will solve any problems that we find as a result of our inspection. We can also help you to save money with our energy evaluation of your premises.
During our evaluations, we do the following:
These are only some of the services that we offer, along with our standard heating and AC services in Fort Worth. Residents of Saginaw and Fort Worth are able to decrease their annual cooling and heating costs and at the same time improve the air quality and their quality of life with one phone call. Our number is (817) 341-5149 and you can find us on the web at our Fort Worth home page.
Contact us today by calling (817) 341-5149 or using our online form to schedule your service.
Michael did a great job with my tune up and filter change. He was pleasant and efficient.
Mark did a great job.
Ryan did an amazing job
Matt was able to explain and show me why I keep having to get my vents clean. He showed me he can turn off the airflow drop outside and it save me money and reduce dust. He also showed some options of air cleaners and ultra violet rays.
Knowledgeable and friendly!
A very nice young man. Very helpful and knowledgeable
He is the best..
Zac did a thorough inspection and the necessary service. He explained the service and costs to my satisfaction.
1st guest bathroom Drain plunger not installed properly is loose but water supply is good, toilet flushes and fills properly as well and shower is good Second guest bathroom All fixtures good in this restroom Outdated water heater.
System is still in new condition amana heat pump with back up stirps. Everything is working like new. Still a very clean system. Changed old filter and broke down condensor to clean. System is now ready for cooling. Also has uv light at the supply air. I recommend another between the blower and evap coil. #solar not interested. Water heater works great to. Thanks for choosing comfort experts.
3/22/23 upon arrival found system heating and cooling with a 20 delta. Goodman amana heat pump. Replaced UV bulb with customer's approval. Drains were slowly draining and I disconnected the p trap and blasted it out with the hose. Added new pipe dope to the start fitting on the coil drain pan and inspected operation. No further issues were found and system was left fully functioning
Performed Stu, system operation is normal, refrigerant levels in range, capacitor in tolerance, amps normal. Moved true suction port away from reversing valve as it was starting to rub, condenser surge protector has failed and burnt up in the disconnect. Disconnected surge protector and installed whole home surge protector.
STU performed today, outdoor unit refrigerant levels are good at this time and the dual run capacitor is testing within manufacturer specifications. Indoor unit filter is clean and the primary drain line is clear at this time, all ignition components are functioning properly and the inducer motor is pulling proper amperage. #solar
Arrived for AHC #solar 6 year old carrier furnace Blower wheel is dusty causing inefficient operation and dust allergies No water safeties present on the system Filter is fine Drain lines are clear Secondary drain pan is beginning to rust through Coil is just starting to have biological growth forming Washed the condenser coil All capacitors are in tolerance Hard start kit recommended to lower compressor starting amperage to manufacturer recommended levels
Amana 4 ton straight cool condenser with gas furnace installed in 2010. Megohm tested compressor showing it has weak windings. Inducer motor on gas furnace has play in bearings and is building up steel dust on the motor coils. Inducer motor needs to be replaced soon. Blower motor is acceptable. Blower wheel and evap coil are clean. Compressor is weak but condenser fan motor is acceptable. Refrigerant and air flow levels are acceptable.
Tune up showed control broad out of tolerance with scorch marks on the back of the control board. Need to order oem control board. This is a over 10 410a system. The zone system has been disabled as well. The system is in working condition and is still pretty clean especially after cooling tune up. Freon levels are on the a little low.
After tune up I replaced double pole contactor on condensor and replaced defrost control board. The system has all its gas its a 4ton heat pump goodman system in clean and healthy shape. #solar not interested at this time and the water heater looks great too. Thansk for choosing comfort experts.
Customer would like a physical copy of his receipt and report sent to his home address. 2021 Goodman heat pump with 2015 carrier air handler. All electrical connections are tight with no corrosion. X13 blower motor is acceptable. Blower wheel is dirty but evap coil is clean. 45/5 dual run capacitor and primary motor start are acceptable. Compressor and condenser fan motor are acceptable. Refrigerant and airflow levels are acceptable.
Call (817) 341-5149 or Message