How well does your Saginaw air conditioning unit perform? Do you feel comfortable when you are at home or does your AC unit require repairs or servicing? Saginaw residents know just who to call when their AC units start acting up. In addition, they also know they can rely on us for AC service in Fort Worth, TX for all their AC needs in Saginaw. We can also help you with the air quality in your home.
If you need Saginaw or Fort Worth AC repair, we can help. Before we even start working, we will give you a free estimate of the cost and the issues that we find. And if you want a second opinion, you don’t have to pay us until after we have completed our AC service call. You can do even more for your AC unit than just getting a service from us. To prevent future Saginaw AC repair service calls, you can sign up for our AC service maintenance agreement to keep your unit maintained regularly. By having regular Saginaw AC service done on your AC unit you can decrease the need for future repairs. Saginaw and Fort Worth residents should be able to use the same unit for as long as they live in the home, provided that the unit is properly maintained. We can provide you with AC service in Saginaw and because we guarantee our work 100%, you have the assurance that you will get your money’s worth. This same guarantee is offered for our heating repairs service. Also, Saginaw and Fort Worth homeowners can depend on us to provide installations and assessments that will enhance the air quality in their homes.
Energy Efficiency and Environmental Quality
We will check your residence for mold, radon, and other hazardous particles in the environment and we will solve any problems that we find as a result of our inspection. We can also help you to save money with our energy evaluation of your premises.
During our evaluations, we do the following:
These are only some of the services that we offer, along with our standard heating and AC services in Fort Worth. Residents of Saginaw and Fort Worth are able to decrease their annual cooling and heating costs and at the same time improve the air quality and their quality of life with one phone call. Our number is (817) 341-5149 and you can find us on the web at our Fort Worth home page.
A very nice young man. Very helpful and knowledgeable
He is the best..
Zac did a thorough inspection and the necessary service. He explained the service and costs to my satisfaction.
Easy, simple and quick. Good to know that everything is in working order!
Called because the A/A stopped working as it should and in a couple of hours, technician arrived, and the A/C is fixed. Love the great service I received from the person who answered the call to the technician.
Appreciate Zak making it out
Yaz was great. He was knowledgeable and very professional (respectful). My AC was working again quickly.
Installed compressor saver, system now pulling 81 amps instead of 140
Found supply plenum disconnected and barely hanging on by tape and a loose nylon strap, plenum was not installed with sheet metal angles to support plenum to case coil, need to return with sheet metal to properly support plenum, for temporary heating and cooling taped plenum to coil
HTU performed today, indoor unit ignition components are functioning properly and the inducer motor is pulling proper amperage. Offered to also check the cooling since the system is about to be out of warranty but customer declined
Primary electrical control, condenser fan motor leaking oil, low refrigerate, evaporator coil rusty corroded and leaking, biological growth, build up on blower wheel, system upgrade do to age condition and efficiency.
STU performed today, outdoor unit refrigerant levels are good at this time and the dual run capacitor to testing within manufacturer specifications, indoor unit filter is clean and primary drain line is clear at this time. Heat strips are pulling proper amperage and the system is working as it should in both heating and cooling. System is pulling over manufacturer rating on start up amperage, recommended a compressor saver to bring it down, customer is going to speak to his wife about it
Tech arrived for a STU. Upon inspection, the capacitor was within specs. The contactor was in working condition. The fan motor had minor rusting. The filter was relatively clean and was not replaced per customer. The blower area and coil was a little dirty. The drain system was clear and bleach was poured. The heating system was functioning. The Delta was within range. The system did not appear to have Surge Protection. A surge protector was installed today and all lights were illuminated. The system was functioning upon departure.
Tech arrived for a filter change. The filter was dirty and replaced. The tech noticed that the ductwork was also dirty. Tech gave a quote for a level 1 duct cleaning 25% off. The system was not evaluated, only a filter change was performed.
Tech arrived for a HTU. Upon inspection the outside capacitors were out of tolerance and the compressor and there was improper wiring methods. The fan was pulling very high amperage above RLA. The compressor was also pulling high amperage. The condenser fins were damaged and bent. The contactor had rusted terminals. The system did not appear to have Surge Protection and the disconnect was broken. This is a pull type disconnect and it was detached from the breaker box casing. The refrigerator tested low per guages, reading a 20 degree low side Sat temp. The Delta was 17 degrees. The ducts and blower area was very dirty. The coil had rust and corrosion present. The blower fan capacitor was out of tolerance. The blower motor was vibrating and labored. The drain system was clear and bleach was poured. Due to the age, condition, price of repairs, and presence of R-22; it is recommended that the customer speak with a Comfort Advisor about upgrading to something more reliable with warrant
Arrived for NH call. Gas valve not staying open, Part ordered
11/18/22 Upon arrival found system heating and cooling. UV bulb was burned out and I recommended the customer get a new one. Customer purchased a new UV bulb. I checked the filter, and it looked okay. The filter wasn't super dirty and I asked the customer if they wanted to change it anyways. Customer said they would wait a little longer before changing it. Cleaned outside condenser coil which was already pretty clean as it was. Cleaned and waxed top. System was left cooling with a 20DT