Farmers Branch AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Farmers Branch home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Farmers Branch AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Farmers Branch AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Farmers Branch families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Farmers Branch, TX
Our Reviews by City
David - Farmers Branch, TX 75234
Blake did a good job checking my HVAC system.
Laura - Farmers Branch, TX 75234
Great and friendly
Great job!! Works wonderfully!
Elizabeth - Farmers Branch, TX 75234
Jhorden really did an excellent job installing the inside components of my new A/C!! He was very thorough and precise. The unit is very neat, stable, and protected. He showed me exactly how to maintain it and assured me he would always be available if I had any questions or problems! He is an outstanding technician!!
Glad I called
Elizabeth - Farmers Branch, TX 75234
Devyn and Danny both did a wonderful job!! They were professional, thorough, explained everything very clearly. They were very easy to work with and they presented me with a package which was perfect for me and my home! I am extremely confident in choosing Comfort Experts!!
Edmund - Farmers Branch, TX 75234
Have always loved these guys
Lamar - Farmers Branch, TX 75234
Connor was very thorough. He went over the recommendations that he had for our system. He also stated the reasons why he would recommend them. He was very personable and kind
Mark did a great job
Mary - Farmers Branch, TX 75234
Very professional. Easy to talk with and answered all my questions. Made sugestions on things to thing about on a later date.
Tech arrived at a warranty tuneup. Upon inspection the capacitors were within specs. The contactor was in working condition. The condenser coils were hosed off to assist with air flow across the coils. There was no observed surge protection. Loose connections were tightened. Low voltage conduit was secured per customer request. The filter was clean. The blower area was a little dirty. The drain was clear and bleach was poured. The UV light was expired. Customer was informed of recommendations today. They would like to move forward with upgrading to an IAQ 200 System and Air Cleaner. We will pause to call to order and install at another time. Customer would like Friday first call if possible. The system was functioning upon departure.
Customer was confused why I was there because she said she didn't even remember calling us out. She mentioned that she has been sick lately and has some issues with recalling. I arrived system was on and cooling properly and still operating upon my departure. Blowing 54 degree air from supply. Cx
Tech arrived at a warranty tuneup. Upon inspection, the capacitor was within specs. The contactorless board was showing normal operation codes. There was no observed surge protection. The Delta was within range. The filter was dirty and there was no replacement today. There was signs of rodents. The insulation levels were low. The drain was clear. The customer was informed of recommendations today. He does not have time for repairs right now. He will review the information and call back for repairs. The system was functioning upon departure.
All three units temperature delta drops were normal, all capacitors tested within range, drains were tested, outdoor coils were washed off, and refrigerant levels normal. Did quote customer for installing a UV system on the upstairs unit. Customer did not want to do repair at this time. Also informed customer that other two uv system bulbs would need to be replaced.
Upon arrival system was not working. No power to indoor unit. Fuse replaced went bad. Replaced fuse , system came on. Please schedule electrician to come out here and inspect why fuse went bad in 2 days. Left system in working condition.
System operating perfectly. Heatload issue
Found blown fuse on in coming power switch swapped and cleaned extremely dirty condenser
Installed new condenser, cut in 4 return grills on bottom of the closet, Un installed furnace and coil, sealed floor, raised furnace and coil and set furnace on a new elevated platform. System operating as intended
Non condensibles in system, compressor failed, hot gas discharge only 145 degrees, furnace is pulling air from under house, not enough return, need to replace compressor or condenser, and lift furnace up and cut in 4 return vents through doors and closet.
On arrival the system was cooling and producing a 17 degree delta. I checked refrigerant levels and the outdoor units cap and everything was in line. Ms Roberts stated that she didn't remember calling us and that everything was working fine and she didn't want me there too long. As I left the system was running and cooling.
Upon arrival the system was running. We adjusted the refrigerant levels and the system is cooling much better now. We also cleaned the outside unit to help cool better. As I left I ensured that both the indoor and outdoor unit was running. Thanks for choosing comfort experts and have a great day!
On arrival the outdoor and indoor units were running. We had a 17 degree delta and the drain lines were clear. All tests on the outdoor unit came back within an acceptable range. The air coming from her vents was 6-7 degrees higher than the air after the coil, which led me to inspect the attic for duct or insulation problems. I diagnosed the 80 degree temp in the house as being a heat load issue that could potentially be rectified by adding insulation and potentially new duct work. As I left I ensured that the outdoor and indoor units were still running and cooling. Thanks for choosing comfort experts and have a great day!
Upon arrival the outdoor and indoor unit were both on and running. The outside unit capicator tested within range, and the systems superheat confirmed that there were no refrigerant issues. The indoor unit had clear drain lines and I flushed them to confirm. The delta at the closet unit was 20 while the delta from the grills and at the thermostat was 10, indicating the 81 degree house hold temp is a insulation or duct issue. I inspected the attic and found that the insulation was 3-4 inches deep and that half of the ducts are older mylar and half are metal. As I left I ensured that the outdoor and indoor unit were still running. Thanks for choosing comfort experts and have a great day.
Tech arrived for a filter change. Customer had the correct 410 AprilAire filter and the filter was replaced today. Customer decided to renew her membership with the same Titanium Membership that she had before.
Arrived on site customer said unit wasn't coming on. Located thermostat thermostat was set to cool at 89 degrees home temp was 81. Performed troubleshooting tests i.e. refrigerant , electrical components, filter was dirty however I don't believe it caused the issue. Upon completion of inspection system has no deficiency that could be found. Asked customer if they had any spare filters if so i would replace while i was there they did not. Advised customer to replace filter as soon as possible. Provided filter fetch info to customer.
Upon arrival the outdoor and indoor unit were both running as intended. The closet unit was clean, the only issue was the filter needs to be changed. The outside unit was clean and in good working order, I recommended a compressor saver kit due to the compressor over amping on start up. When I left both systems were in good working condition. Thanks for choosing comfort experts and have a great day!
Customer doesn't want to go forward with work at this time There is 9 shot off valve that will not shot off
Went to house for stu on two year old gas furnace system. Checked furnace in heating,flame sensor and ignitor working, filter is dirty, customer getting new filter when possible, blower dirty, recommended blower clean, electrical connections good. Unit has wet switch, recommend drain switch for complete water protection. Evaporator coil is clean, unit is operational in heating, went to outdoor unit to check cooling. Fan amps are fine, compressor amps are good, recommend compressor saver to decrease starting amps, capacitor within tolerance, electrical connections stable. Washed condensor coil, unit is operational in cooling.
Customer was not aware that this was plumbing tune up but decided to proceed, everything good except water heater is working but is from 08 Customer would like HVAC tune up done asap
Arrived at location and spoke with home owner. Inspected indoor unit. Blower clean. Coil clean and in good condition. Electrical connections tight. Temperature delta within acceptable range. Changed filter. Recommended drain pan treatment strip. Inspected outdoor unit. Electrical connections tight. Capacitor in spec. Coil in good condition. Refigerant charge good. Washed coil. Fan and compressor Amp draw good. Recommended compressor saver and either unit or home panel surge protection.
Tech arrived for a tuneup. Upon arrival the customer mentioned that there was water around a vent in the front room. There was a tarp on the roof above this area. The ceiling and vent was scanned with the infrared FLIR camera. There did not appear to active moisture in this area at this time. There have been recent severe storms in the area. She has an insurance adjuster coming out next week to evaluate. The filter was recently replaced. The ductwork was a little dirty along with the blower motor. The drain was clear and bleach was poured. There was no inline drain safety. The capacitor was within specs. The Delta was 19 degrees. The contactor was in working condition. The condenser coils were very dirty and were hosed off to assist with air flow across the coils. There was no observed surge protection. The customer will speak with her husband and let us know what they decide. The customer is aware that there may be an additional service fee if we have to return for repairs. The cus
Checked both inside and outside Goodman units. Inside unit electricals we're good. Connections were sound. Ducts and blower had build up of dirt and other debree. Ducts and blower need cleaning, explained benifets of duct cleaning and overall cleaning to customer. Outside unit is performing well. Amp draws are in range. Capacitor is within tolerances. Cleaned outside coil. System left in working order. Customer did not have supplied filter
Came out to a super tune up walked inside check the thermostat looked at the inside unit that cleanse is good very clean family also the family that lives here are tenants not homeowners replace the filter looked at the insulation inside the attic it is filled to the t did amp draws educated the customer a little bit couldn't get a hold of the homeowner went outside Washington cleaned the unit check freons check the amp draws temperature split is good everything is running accordingly going to get a hold of the homeowner to make decision
Tech arrived at a STU*3. Main Area System- The capacitor was within specs. The contactor was in working condition. The coils were clean but hosed off anyways. The Delta was at acceptable levels. The filter was clean. The heating system reached complete ignition. The UVV system was functioning. The drain was clear and bleach was poured. Sump pump was functioning. The thermostat was not switching into Cooling mode. The customer reprogramed the thermostat and the cooling system responded as intended. Upstairs system- The capacitor was within specs. The contactor was in working condition. The coils were clean but hosed off. The Delta was at acceptable levels. The filter was clean. The heating system reached complete ignition. The UVV system was functioning. The drain was clear and bleach was poured. Bedroom system- The capacitor was within specs. The contactor was in working condition. The coils were clean but were still hosed off. The Delta was at acceptable levels. The filter was
Checked inside and outside system. Inside system is looking good. Blower is also clean. Amp draws and readings are performing good. Outside unit is also good. Contactor was buzzing, replaced with new one. Capacitor looks good and is in tolerance. Added a hard start kit. Amp draws are in range. Cleaned outside coil. System left in working order