Duncanville AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Duncanville home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Duncanville AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Duncanville AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Duncanville families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Duncanville, TX
Our Reviews by City
Darrell - Duncanville, TX 75137
Great service! Thanks
Good service, good price
Allan - Duncanville, TX 75116
Very effective and quick to do his job. Very polite
Main: Primary electrical control, evaporator coil rusty and corroded, mylar duct falling apart, filter dirty, build up on blower wheel, duct cleaning. Bedroom: stick stabbed into condenser coil, low refrigerate, evaporator coil rusty and corroded, primary electrical control, build up on blower wheel, blower motor, system upgrade do to age condition and efficiency.
On arrival both systems were running and cooling effectively. The indoor units were in good shape, clear drain lines and a good delta for both systems. The older Goodman system could benefit from a blower cleaning but is otherwise in good shape. We washed and waxed both outdoor units. The newer system had no issues, I did recommend a compressor saver kit to prolong the life of his new system. The Goodman outside unit was over amping the compressor on start up. The max rated amps for the system is 73 and we were pulling 88.9. I again recommended the compressor saver kit to help extend the life of the system. As we left we insured that both systems were on and cooling as intended. Thanks for choosing comfort experts and have a great day!
Upon arrival found system heating and cooling with a 20 delta. Filter was dirty and customer didn't have the right size of filter available. Helped customer order the correct size of filter (aprilaire 410) and she is going to change the filter herself. Recommended replacement of the UV bulb, installation of compressor saver, and surge protection. Customer approved all of these and renewed her membership. System was left cooling with a 20 delta
Upon arrival for tune up system on and cooling. Inspected indoor unit. Drain line clear. Changed filter. Furnace inducer motor rusted. Growth on blower. Heavy corrosion on coil. Inspected outdoor unit. Using old refrigerant. Fan and compressor amp draw high but within unit specifications. Recommended repairs or replacement of unit. Customer declined at this time.
Upon arrival found plenum insulation soaking wet top to bottom, in attic found insulation on metal plenum had fallen off causing condensation, need to fix insulation in attic and re wrap plenum and seal air leaks at plenum.
Performed ctu, system is in poor condition, evaporator coil is severely rusted and corroded, compressor is drawing extremely high amps, system is low on r22, system had a 32 superheat, calling for a 6. Blower motor is leaking oil and has play in the bearings, cleaned condenser coil. Customer is going to contact home warranty, recommend system replacement.
Customer has 3 systems and all are around 20 years old. He is shopping to replace all 3. The smallest system is currently down. He is looking to make a decision within the next week. quotes for level 1 and 2 were emailed to customer.
Main: primary electric control, Build up on blower wheel, filter dirty and falling apart, evaporator coil rusty and corroded, biological growth in system plenum, Mylar duct taped and falling apart.Duct cleaning. Bedroom: blower motor, build up on blower wheel, evaporator coil rusty corroded and dirty, biological growth, duct cleaning, primary electric control,
Condenser fan motor leaking oil, primary electric control burnt and pitted, blower motor leaking oil, build up on blower wheel, evaporator coil rusty corroded and known leak, heat exchanger has thermal spots and rusty, biological growth in supply plenum, system upgrade do to age condition and refrigerant phase out. Comfort advisor 3-4-22 10-12.
Completed AH tune-up on system and found the flame sensor and igniter have carbon build-up on them. Informed customer of findings and recommended replacing. Customer declined repairs at this time. Customer also had concern of cold air coming from return vent. I tried to feel cool air coming from it but couldn't. Air filter is good, drain line clear and all other heating components ops checked good.
Performed htu. System operating normally. Found compressor capacitor completely failed and burnt the center wire. Customer is going to contact home warranty to get repair taken care of
Blower motor leaking oil, build up on blower wheel, evaporator coil rusty and corroded, biological growth, ignitor, system upgrade do to age condition and refrigerant phase out. Replaced filter provided, 2-8-22 6-8.