Mckinney AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Mckinney home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Mckinney AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Mckinney AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Mckinney families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Mckinney, TX
Our Reviews by City
Andrew - McKinney, TX 75070
Blake did a great service, he explain in detail what we needed and why we needed it.
Gail - McKinney, TX 75071
Timely, professional, and helpful
Tommy - McKinney, TX 75070
Rebecca - McKinney, TX 75069
Marcy - McKinney, TX 75070
Ryan was very professional, friendly, and efficient. His explanation of what he found was very clear.
Felicia - McKinney, TX 75071
Great service, Devyn!
Gavin - McKinney, TX 75070
Devyn quickly diagnosed and resolved our AC issue. Great service.
Very quick and efficient. Polite young man
Jim - McKinney, TX 75070
Gail - McKinney, TX 75071
Always good service and professional technicians
Response from Comfort Experts Inc.:
Thank you for trusting us to get the job done. Your 5-star review and gratitude mean a lot to us!
Great professional service
Robert - McKinney, TX 75070
Casey did a thorough job troubleshooting and repairing our A/C system. He also checked the entire system to make sure everything was working properly.
Response from Comfort Experts Inc.:
Thank you Robert!
Marcy - McKinney, TX 75070
Very nice, friendly, knowledgeable rep! Very good service and explanation.
Lennice - McKinney, TX 75071
Job well done. Very satisfied with the service Casey provided
Guy - McKinney, TX 75071
Simon was an awesome tech who explained everything before he started working and then went over everything throughly afterwards. We've used this company for 10+ years and have always had excellent customer service both on the phone and in person.
As far as I know, Tyler did an excellent job. He said everything he checked out was fine.
Mary - McKinney, TX 75070
Robert - McKinney, TX 75070
Bruce - McKinney, TX 75069
The tech did good.
They did a very clean and thorough install and they also, went over everything completely ly understood. We appreciate their professionalism and thei
Roosevelt - McKinney, TX 75070
We are very happy
Homeowner - McKinney, TX 75070
Erasmo did an awesome job.
Kaye - McKinney, TX 75069
Accommodating schedule, on-time, courteous & pleasant, did an excellent job of servicing, as well as I could tell.
On arrival the system was running and cooling. I installed the new fan motor and capicator. Once finished the system turned back on and resumed cooling. Thanks for choosing comfort experts and have a great day!
Tech arrived at a membership tune-up. Upon inspection the capacitor was within specs. The contactorless board showed no errors. The system had surge protection. There is whole home surge protection at the main panel. The Superheat was very low. Possible TXV malfunction. The Delta was a little low. The filter was dirty and replaced. The drain was draining slowly. A treatment strip was added today. The water heater flue pipe was misaligned. Attempts were made to center the flue but were unsuccessful. The customer was informed of recommendations today. The customer would like a plumber to evaluate the water heater and other house plumbing fixtures. She is available Monday, she has to leave at 1:30pm. The repair needed is a possibLe safety concern. We will pause the call for a visit from a plumber.
Need to return next Wednesday afternoon with a 1/6 hp 825 rpm condenser fan motor. I do not have one in the van so I am setting it up as rec work.
9/20/23 Will be returning the 26th with added work a new cover plate and a half switch half duplex switch cover plate for the new light
Returning Wed 20th to finish
Furnace operating efficiently and safely, blower wheel clean and operating efficiently, compressor Amp draws acceptable Fan motor Amp draws acceptable System clean and sfe
Tech arrived at a warranty tuneup. Upon inspection the capacitor was within specs. The contactor was in working condition. The condenser coils were hosed off to assist with air flow across the coils. The filter was dirty and replaced. The blower area was dirty. There was growth throughout the system. The UV bulb was not functioning. The house power went out during the inspection. The customer was informed of recommendations today. House power was still off upon departure.
Tech arrived at a service call. Upon inspection, the capacitor was out of tolerance. The contactor was buzzing loudly and had rusted terminals. These two items were replaced today and the system regained functionality.
Tech arrived at a membership tune-up. Upon inspection, the capacitor was within specs. The contactor was in working condition. The condenser coils were hosed off to assist with air flow across the coils. The filter was dirty and replaced. The Delta was within range. The drain was clogged and there was water in the secondary drain pan. The drain was cleared and a treatment strip was added to help keep the drain system clean. The insulation levels were low.
Tech arrived at a warranty service call. Upon inspection, the thermostat was blank. The furnace control board was recieving high voltage. The neutral was not recieving properly continuity through the transformer. The high voltage connections were tightened and the system regained functionality. The Delta was 21 degrees. The UV bulb was replaced and a treatment strip was added to help keep the drain system clean. The system was functioning upon departure.
Upon arrival system was in working condition. Client stated that company that installed units diagnosed and bad txv and recommended recovery refrigerant and putting in new refrigeratant cause it was ' contaminated ' told client that if refrigerant was contaminated, system would not have been able to work 5 yrs. Left system In working condition. Client had invoice.
Upon arrival both systems were in working condition. Looking at the indoor units all electrical connections and components are good. Blower and coils are clean. Drain lines are clear and flowing. Looking at the outdoor units , all electrical connections and components are good. Both capacitors are within tolerance. Downstairs unit could benefit from compressor saver. Refrigerant levels are good. Amp draws are good. Cleaned both units inside out. Left both systems in working condition. Thank you for choosing comfort experts.
Arrived for service eval Error code for open start circuit Dual run cap testing at 0 Hard start kit blown Replaced both System operational Ran for 10 minutes to verify refrigerant is at good levels UV bulb is out of date and should be replaced or upgraded to a 5 year UV system No surge protection present on furnace - recommended to protect control board - install at furnace or onto the house panel All repairs approved by the homeowners son
Tech arrived at a membership service call. Upon inspection the wet switch was tripped. The wet switch was relocated. The drain was tested and found to be clogged. The drain was cleared and a treatment strip was installed. The system was functioning upon departure.
Upon arrival for service system on and cooling. Customer states thermostat losing power off and on. Inspected safteys on system. Found partial clog in drain lines which would cause power loss then slowly drain after 30-40 min allowing power to return. Cleared and sanitized Drain line. Left system on and cooling.
Tech arrived at a service call. Upon arrival it was late. The customer mentioned that both systems were not functioning properly. Upstairs system- the Delta was 10 degrees. The condenser coils were very dirty. There was a 10 degree Superheat, 3 degree Subcool. A leak search was performed. There was a possible leak at the interior portion of the condenser coil at the bottom. Downstairs system- there was a L6 code for Open Start Circuit Lockout. Capacitor was out of tolerance and was replaced today. The customer previously purchased a premium capacitor. The capacitor was replaced under warranty. The condenser coils were dirty and were replaced today. The customer was informed of recommendations. He will contact his warranty company about the upstairs system. The systems were functioning upon departure.
Quoted 36k coil only $4,184
Arrived for service eval System low on refrigerant Filter fine Blower is good Coil leaking Tons of bio growth in the supply plenum Unit disconnect breaker failed while on site CA set for 5/31 10-12
Complete STU on R22 system 09, upstairs unit only heatpump. Heating was not check per customer request. No obvious issues or know issues with heating per customer. No obvious signs of heating issues. Cooling mood was checked. 18 degree delta, indoor coil clean, blower motor, squirrel cage and blower capacitor ok. Blower cap is 15 mfd within manufacturer specs. Drain functioning as should. Poured 1 gallon of water through drain without issues. Customer provided air filter changed. Outdoor unit fan amps, compressor amps ok, fan motor was pretty warm indicating its weak. Capacitor was ok. Within manufacturer specs. Outdoor condenser full cotton tree blooms. Unit was cleaned and washed. Refrigerant levels slightly low. Saturation levels above freezing. R22 system. Recommend replacing contactor, customer declined. Technician will need a 8 ft ladder to access upstairs unit.
Tech arrived for a membership tune-up. Upon inspection the capacitor was within specs. The contactor was audibly buzzing. This item was replaced today. The Delta was within range. The system did not appear to have surge protection. A unit surge protector was installed today. The filter was replaced. The drain system was found to be clogged when testing. Multiple clogs were found and removed from the drain system. A drain treatment strip was also added to help keep the drain system clean. The customer inqured about having the disposal and a couple faucets replaced. The customer was given a quote and will call us back at a later time once he decides how he would like to proceed. The system was functioning upon departure.
Upon arrival for service customer states noticed system not cooling yesterday. System was blowing air but outside unit was not coming on. System off at breakers. Turned system on and system came on and cooled. Cleaned system. Drain lines clear. Refrigerant pressure good. Electrical conections good. Capacitor within tolerance. Left system on and cooling at departure.
Arrived on site greeted cx thanked them for continued membership and business. Moved to outdoor package unit tested all components all measured within ratings and specs. Blower wheel, coil and drain are clean and clear at this time. Refrigerant level is normal. Washed and cleaned unit. Uv light bulb was not working offered replacement. Cx politely declined today.
Outdoor unit is operating within specifications, refrigerant levels are good at this time, capis out of tolerance ,indoor unit is operating within specifications, safety checked and are good, drain line is clear at this time, replaced cap, custo,er needed to talk to someone else about other recommendations
Arrived at location. Home owner not present. Someone else was sent to let me inside. She then left. Inspected indoor unit. Electrical connections tight. Temperature delta within acceptable range. Blower wheel clean. Coil clean and in good condition. Changed filter. Inspected outdoor unit. Electrical connections tight. Refrigerant charge good. Coil in good condition. Washed coil. Fan and compressor Amp draw good. Capacitor in spec.
Arrived for CTU #IAQ 4 year old goodman furnace Replaced filter Sitting water in the primary drain pan - declined drain clear today Slightly dusty blower Coil is clean Dust and biological growth in the supply plenum - UV system air scrubber recommended for clean air 20 degree delta Washed condenser coil Capacitor in tolerance Running amp draw is in range Compressor starting amperage over manufacturer specs and should be lowered with a compressor saver kit - rated up to 112 measured at 140