Savannah AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Savannah home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Savannah AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Savannah AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Savannah families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Savannah, TX
Our Reviews by City
Tested all components all measured within ratings and specs. Refrigerant level is normal. Washed and cleaned both outdoor units. Changed filters.
Control board is faulty holding for parts
Tech arrived for a warranty no cool. There was a ride along employee present. Upon inspection the outside system was not recieving high or low voltage. The breaker at the main panel was tripped. The motors, wiring and contactorless board was isolated to identify the cause of the trip. The compressor has continuity to ground and tripped the breaker when plugged in. A replacement compressor will be ordered and installed at a later date. The outside unit was left in the off position and the attic unit was updated. Emerson Copland Scroll Compressor Model# ZPS29K6E-PFV-130 SERIAL# 19A61E45L
Tech arrived for a tuneup. Upon inspection the capacitor was within specs. The contactor was in working condition. The condenser coils were dirty and were hosed off to assist with air flow across the coils. The system did not appear to have Surge Protection. The filter was dirty and replaced. The blower area was also dirty. The drain system was clear and bleach was poured. The heating system reached complete ignition. The insulation was low in the attic area. The upstairs thermostat batteries were replaced. The customer asked the tech to see if he could get the pilot light lit on the fireplace. The fireplace was evaluated and the tech was able to get the system function. The customer was give quotes and information on recommendations. The customer is interested in #Solar, however they are not ready to move forward with an Energy Audit at this time. They will discuss insulation upgrade and surge protection for another visit. The system was functioning upon departure.
Rewired all receptacles and fan light combos. Fixed tripping breaker
Tech arrived for a STU*2, no cool. Upon inspection the outside units were extremely dirty and were hosed off to assist with air flow across the coils. Upstairs system- The capacitor was close to being out of tolerance and was replaced. There was an error code for Compressor Protector. Compressor Saver was replaced. The Superheat was 14 and the Subcool was 6 with a TXV metering device The UV light was functioning. Downstairs system- The capacitor was close to being out of tolerance and was replaced. The contactor was in working condition. Delta and refrigerant was at acceptable levels. The UV light was not working. The filters were dirty. Drain systems were checked and clear. Customer asked about adding unit surge protection. A quote was given and the customer will budget for purchase on a later visit. Both systems were functioning upon departure.
Arrived for Leaky drain call Secondary drain pan is dry Secondary drain line links up with drain pan line - leaking Compressor is not coming on Capacitor in tolerance compressor entered thermal overload Dirty filter caused compressor issues Swapped in new filter Charge is good. Unit running fine