A leak needs to be inspected carefully. Any liquid you see in or around your heating or AC units shouldn’t be ignored. It may be water or refrigerant, it could be condensation from normal use, or it could be a problem with the system. If this is an issue you are facing and you are in Colleyville, TX, AC repair and heating repair should be taken care of by a local AC repair company, like Comfort Experts. Here are a few things
Your air conditioning unit should never be low on refrigerant. It is a closed system, which means the refrigerant is passed through the system constantly and never runs down or becomes ‘used up’. If your refrigerant is low – either your air conditioner wasn’t set up properly or you have a leak.
If you know your air conditioner had sufficient refrigerant when you’ve used it previously, then you most likely have a leak. You should never attempt to replace or clean up and dispose of refrigerant yourself. The refrigerant used in air conditioning systems is a pollutant and should be handled by a qualified AC repair technician.
If your AC and heating repair tech simply tops up your refrigerant and a leak is the problem, then it will leak again. He or she needs to thoroughly inspect the system to identify the leak, which is what we will do when you call us. A quality AC repair tech will check multiple areas of your unit to identify the source of the leak or other issue.
There are a number of reasons why water could be coming from your air conditioning unit. Many can be prevented during a regular service, but if you haven’t had your system serviced recently, there are number of things that could be causing the leak.
If you have used your air conditioning system with no problems and suddenly find liquid that is pooling near the unit, don’t ignore it! Even if it is just water, it could be a symptom of a bigger problem. You can take steps to prevent the most common problems by servicing your air conditioning annually.
Had a great experience. Did the tune up on units and felt very at ease. He was efficient and friendly.
Brian was polite, efficient, and very knowledgeable. Very friendly and answered all our questions. Neat work and cleaned up areas. We love this company and have been working with them since they put in our Heat Pump.
A Goodman rectifier is less than $5 bucks on Amazon I paid Hobson over $200. Hobson has done this more than once. Shame on you. Technician was fine
I contracted with Hobson Electric to have a full home generator installed early this summer. We have struggled with multiple supply chain/product availability/ Covid related issues, but I have always been impressed with any of their team members that supported us during this timeframe, and that is doubled for members of the Hobson family such as Brian who personally executed the generator installation , electrical hookup, and our connection to wifi.
Fast quality service
Response from Comfort Experts Inc.:
Thank you David!
Service exceeded expectation
Desmond was very helpful and explained what was going on to our understanding. He was able to get heat to or home during that winter blast that we just had.
Found the service disconnect to the downstairs unit off. After turning the disconnect back on, the unit started cooling the downstairs. Everything at the oudoor unit checked out fine. I advised the homeowner to keep an eye on the service disconnects.
Customer interested in duct cleanings and stove exhaust replacement. Getting quote for stove exhaust and will call the customer back.
Level 2-60k gas horizontal with slab, safety disconnect, drain pan with float switch Clean both duct systems Level 1 duct cleanings with fogger
Inspected system, found drain line clogged, ceiling damage from system leaking outside of drain pan. Customer purchased drain safety and clearing, installed safety and cleared drain. System functioning properly, customer would like to speak to management tomorrow.
Did a STU, changed filter, flushed drain, refrigerant levels are good, customer verified unit was working properly
L1 gas 30k horizontal with disconnect and whip
Upon arrival found found system operating and only outputting a 1 degree delta. Compressor has Mechanical failure, and is not pumping refrigerant. Customer wants to speak with comfort advisor.
Performed super tune up on 3 systems. Verified proper operation in heat. Verified proper operation in cool. Checked electrical components, connections and amp draws. Checked drainage, filter and cleaned condenser coil. Everything is operational at this time. Thank you for trusting comfort experts for your hvac needs. Your technician today was Greg.
Low 410a. Reached sub of 8. Small leak in every coil.
Downstairs Carrie inverter system the has .06 DC voltage communication system. 410a. Sub 8 x-13 within spec. Upstairs drain line clear. X-13 within manufacture spec. Mild bio growth. 410a subcool 10. Cleaned both hps.