HVAC, Plumbing and Electrical Services Near Euless, TX
Comfort Experts Inc. has been the trusted air conditioning, heating, plumbing and electrical service provider in Euless, TX, for over 60 years! Our team of qualified technicians provides reliable, effective solutions for all your home comfort needs. We are available 24/7 for any emergency that may arise. We proudly stand behind our services with a satisfaction guarantee – take a look at our many reviews below to learn more about what we can do for you! With Comfort Experts Inc., you can be sure your home is taken care of promptly and professionally.
Euless, TX AC and Heating Repair Service
Are you frustrated with too many AC or heating repairs? Are you tired of dealing with unreliable, dishonest repair companies? If the answer is yes, then it is time to consider working with the pros at Comfort Experts. Our trustworthy, experienced technicians have helped homeowners with HVAC repairs for years. We work with you to make AC and heating repairs as quick and as seamless as possible so you can rest easy once again knowing that your home will be the perfect temperature for your comfort level.
How Do I Choose the Right AC Repair Company?
When deciding upon the right repair company, you will want to pay close attention to details to ensure you receive the best service at an affordable cost to you. Experience is critical for ac repair technicians. At Comfort Experts, our AC and heating repair technicians are fully licensed, highly qualified and professionally trained to handle any and all repairs that you may need.
No matter what part of your HVAC system needs work, our technician will locate the problem and provide excellent service. We don’t leave until the job is done correctly. A company’s reputation speaks volumes, and at Comfort Experts, we take pride in our reputable services. No job is complete until you, our customers, are highly satisfied. Our technicians take the time to carefully assess the issue, walk you, the homeowner, through the repair process and double-check our work to make sure your AC or heating system is working properly. Our efficient repairs ensure that your unit will last, saving you time and money in the future.
What Should I Expect From a Comfort Expert Technician?
We know that sometimes the unexpected will happen, such as the AC going out in the dead heat of summer or the heater no longer working during one of the coldest weeks of winter. At Comfort Experts, our AC and heating repair technicians in Euless strive to be prompt and efficient to get your HVAC system working once again. Because customers are our number one priority, our repair technicians are always upfront and honest about necessary repairs and expenses.
Sometimes, repair costs can add up, causing unwanted stress. At Comfort Experts, we work with you to make repairs affordable, even offering financing to help balance out the larger expenses. Our friendly, trustworthy team is always available to answer any questions you may have. There’s a reason we are a top-rated AC and heating repair company in Euless, TX. Come find out for yourself all that we have to offer our customers. Call us today at 817-341-5149 !
for Euless, TX
Our Reviews by City
Very good service prompt and timely
Am - Euless, TX 76040
Ali S. - Euless, TX 76040
Great Service, Awesome Price, A+ for their technitian Michael Spalding !!
Claudia - Euless, TX 76039
Darrell - Euless, TX 76040
Jeff was very professional and did a great job diagnosing the problem and fixing it in a short time.
Lissa - Euless, TX 76040
Meet - Euless, TX 76039
Professional and customer friendly tech
AC tuneup/Electrical check
Todd - Euless, TX 76040
We were expecting an AC tuneup / check. Tyler didn’t look at the AC system but validated our electrical plugs, etc. If we were supposed to have an electrical checkup, Tyler did a great job. 10-5 is too big of a window. I received a text that Tyler was on his way, but he didn’t show up for another hour.
Great Services with cares
Anna - Euless, TX 76040
Great job and like agents who take a care of my place
Marchellea - Euless, TX 76040
Gavin was informative and friendly. My family and I are happy that he was chosen to come out and service our unit. He was efficient and seemed to enjoy the work he was doing. 5 stars!
Jill - Euless, TX 76039
William - Euless, TX 76040
CRAIG was awesome and thorough.
Am - Euless, TX 76040
David - Euless, TX 76040
Friendly and knowledgeable technician that gave a complete update on my AC systems.
Vickie - Euless, TX 76039
I appreciate the professional service and professionalism of the techs!
Corinne - Euless, TX 76039
I’ve been with this company for over a decade. I can highly recommend them for good and fair service from knowledgeable, hard working servicemen.
Technician was professional & courteous
Mary - Euless, TX 76039
would be nice if invoice showed total price and discount received due to being plan member
Antoinette - Euless, TX 76040
Technician was polite and professional.
M.J. - Euless, TX 76040
Mary - Euless, TX 76039
Mary - Euless, TX 76039
Katie - Euless, TX 76040
He was very polite and professional
CSS - Euless, TX 76039
Did a good job. Worked efficiently and quickly.
Mary - Euless, TX 76039
Very professional; provided explanation and took care to cover shoes.
Peggy - Euless, TX 76040
What a nice young man, very knowledgeable, helpful and kind...so appreciated his help and expertise, an excellent representative of his company...
Regina - Euless, TX 76040
09/22/23 Tyler S - master bathroom double vanity sink has a clog in the middle where they meet behind wall. After trying multi options to unclog, the only remaining option for us is too open the wall and cut open pipe blow the T then after unclogging repair the cut pipe. We are not acceptable for any drywall repair after.
Outdoor unit is operating within specifications, refrigerant levels are good at this time, indoor unit was operating within specifications, drain line is clear at this time, customer declined all recommendations, left system cooling
Systems are in working order. 1 is much older then the other and needs some part replacements. Customer does not want to put money into the old rheem and would rather replace the system next year.
Tested all components all measured within ratings and specs. Refrigerant level is normal. Washed and cleaned outdoor unit. Changed filter.
Tested all components all measured within ratings and specs. Refrigerant level is normal. Washed and cleaned both outdoor units. Changed filters.
Customer needs time to think wanted quotes will follow up with her in 2 weeks
Tech arrived at a STU. Upon inspection, the capacitor was within specs. The contactor was in working condition. The condenser coils were hosed off to assist with air flow across the coils. There was no observed surge protection. The Delta was within range. The insulation levels were a little low. There was no observed drain safety. The drain was clear. The customer was not present. She was sent estimate recommendations. The system was functioning upon departure.
Upon arrival system was in working condition. Client was not home but just wanted his thermostat replaced. Thermostat was replaced. Outdoor coil is really dirty , offered a coil clean but rejected work. Client paid through phone. Left system in working condition.
Upon arrival system was in working condition. Client stated that before leaving for vacation system was cooling properly. Coming back system was not cooling properly. Looking at the outdoor unit , unit was running on a very low capacitor. Went ahead and replaced it , system is cooling properly. Left system in working condition.
Customer was told they needed to replace coil and replace line set because it was smaller than 3/8 system was on and cooling well upon my arrival and I detected no signs of a leak of refrigerant as a result of my inspection.
Tech arrived at a warranty service call. Upon inspection, the capacitor was out of tolerance and was replaced. The compressor was in thermal. Core sensor was bypassed. A compressor saver was installed today to help the startup amperage. The attic insulation has settled. The tech recommended insulation and sent an email quote. The system was functioning upon departure.
Replaced motor with OEM. This is a blower motor for an upflow
Moved to outdoor unit tested all components all measured within ratings and specs. Refrigerant level is normal. Washed and cleaned condenser. Moved to indoor unit tested all components all measured within ratings and specs. Filter was really dirty customer did not have replacement I advised to change asap. Blower coil and drain are clean and clear at this time. Recommend compressor saver and drain switch.
On arrival the system was running and cooling. The indoor unit had a 14 degree delta, clear drain lines, and a clean blower and coil. The outdoor unit passed all electrical tests and was fairly clean. I recommended resealing and mechanically attracting a few ducts to the supply plenum to stop air leaking, and I recommended repositioning her master bedroom duct to increase airflow to her bedroom. I recommended a compressor saver kit to increase the life of the compressor and promote energy efficiency, and I strongly recommend installing a drain switch to prevent flooding in the attic. I have scheduled a follow up to speak with the customer and schedule rec work for next week. Thank you for choosing comfort experts and have a great day.
Upon arrival for service system off. System is 9 years old. Confirmed second opinion. Customer states previous tech said pressure on system was severely low inspected system and found no refrigerant in system. Recommended speaking with engineer due to age of system and cost of repairs.
2011 4 ton Lennox HP. Utilized the 410 1lb but it did not bring the subcool up, this is after I washed outside coils. Customer is aware of the rust on the evaporator coil, blocked intake side of coil, very dirty blower wheel, heavy biological growth, no flood protection, Blower capacitor is failing. Outdoor unit was washed, dual run cap failing, Vapor line Insulation is poor, subcool is very low, utilized 1lb of 410 per the call type and that didn't bring my subcool up any. Discussed with the customer about the next steps, built estimates showing membership benefits. Customer wants to explore the route of a new system since they have no manufacturer warranty. CA appointment 7/15/23 @8am confirmed.
Upon arrival for tune up system on and cooling. Inspected outdoor unit. Fan and compressor amp draw within unit specifications. Capacitor within tolerance but barely. Refrigerant pressure high. Cleaned unit. Refrigerant pressure returned to normal levels. Inspected indoor unit. Blowers has slight dust buildup. Coil clean. Drain line clear. Recommended replacement of capacitor. Left system on and cooling.
Tech arrived for a tuneup. Upon inspection the capacitor was out of tolerance. The contactor was in working condition. Condenser coils were dirty and were hosed off to assist with air flow across the coils. There was no observed surge protection. The indoor coil and blower area was dirty. The drain system was flowing slowly. The customer was informed of recommendations today. She decided to move forward with adding a drain treatment strip today. Her son is in HVAC and will take care of the capacitor. If she can not get him out in the next month, she will call us back out for the repair. The system was functioning upon departure.
Install 36k upflow gas use current filtration
Upon arrival system was turned off. Turn system on. Upstairs unit turns on but outdoor doesn't. Looking at the outdoor unit , capacitor is out of tolerance. Brought to clients attention, client has P&L , went ahead and replaced it. Outdoor unit came on. Left system in working condition. Thank you for choosing comfort experts.
Arrived at location and spoke with home owner. Home owner indicated system not cooling properly. Inspected system. Capacitor out of spec. Recommended replacement. Home owner agreed. Replaced capacitor. System operating and cooling properly upon departure.
Upon arrival, no cool to the upstairs unit. Customer had installed thermostat by themselves and blew a fuse and also the thermostat was bad. Transformer was bad. Customer declined repairs and is getting a second opinion.
Upon arrival system was working. Customer says they the outdoor unit turns off and the indoor would stay on. Looking at the outside unit , hooked up gauges and head pressure was high. Went ahead and cleaned outdoor unit. Checked the indoor unit blower and coil for air flow restriction but no restriction there. Filters were changed this month. Turned unit back on and head pressure went down. Offered membership but said they would think about. Recommended duct cleaning but they'll also think about. Left system in working condition. Thank you for choosing comfort experts.
Master side of the home had poor airflow. In the attic, I found the duct feeding the master side of the home to be kinked and some of the duckwork coming off the mixing box to be kinked. I rehung the main supply duct to insure there was no kinks. I also rerouted one of the master bedroom ducts to a better position at the air mixing box. The master bedroom, master bathroom, master closet and the laundry room now have better airflow.
Amp draw for fan is high, compressor amp draw is good, capacitor is good. System has leak. Customer did not have time for leak search. Cleaned outside unit and condenser.