Comfort Experts promises customer service that exceeds the expectations of Keene, TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Keene TX.
Response from Comfort Experts Inc.:
Thanks for the glowing review!
Very positive experience.
Upon arrival found d system running and cooling. Delta drop was within range and refigerant levels looked great. Dual capacitor was right at line 9f manufacturers specs. Customer opted to not replace today. All other components were within specs and working properly.
Main: Primary electric control, blower motor leaking oil, covered in debris, build up on blower wheel, evaporator coil rusty and corroded, biological growth, duct cleaning, system upgrade do to age condition and refrigerant phase out. Bedroom: evaporator coil rusty and corroded, biological growth, system rejuvenation, system upgrade do to age condition and refrigerant phase out.
Performed tune up today, inspected all components and washed outdoor coil. Heat pump core sense was tripped with pressure cycling lockout. Reset and verified refrigerant levels are operating properly, showed customer that the dual run capacitor is testing under specs, system drained 1 gallon of water properly. Replaced the dual run capacitor parts warranty, system is functioning properly left on in cooling.
Primary electric control, blower motor leaking oil, build up on blower wheel, inducer motor, flame sensor, ignitor, drain protection, gas line code upgrade, evaporator coil rusty corroded and dirty, heat exchanger has thermal spots and rusty, system upgrade do to age condition and refrigerant phase out.
System is operating normally at this time.
Performed stu. System functional in both heating and cooling at arrival. Client regularly changes filter. Drains flushed and clear. Indoor, coil clean, motor in good condition, heat strips test well. Tightened eletrical connections. Outdoor, charge adequate, defrost and reversing valve functions as designed. Capacitor testing in range, proper amp draw. Cleaned off equipment. System running at departure.
Thoroughly performed a heating tune up, tightened electrical connections and checked all components. Refrigerant levels are good, dual run readings within specs, condenser fan has several hot spots, compressor amps good, air handler has a lot of biological growth and the heat strips are functioning properly at this time. Spoke with customer about system upgrading and adding a generator, customer is waiting at the moment.I Set call back reminder.
Costumer wasnâ€™t at home, got code to get in, rehang duct work fix insulation underneath.
Cleared clogged drain line
Installed already made condensate drains and put in 15amp breaker and showed customer where primary drain line goes into sink in master bedroom