HVAC, Plumber and Electrical Service Near Corinth, TX
At Comfort Experts Inc., we understand how critical air conditioning, plumbing, heating and electric services are for your home. That is why we provide 24/7 services to our customers in Corinth, TX, so you never have to worry about not being taken care of. Our team members are highly trained and experienced in HVAC services. Our plumbing department offers an array of services such as sewer line cleaning, water heater installation and other necessary jobs. Our electrical team provides a wide variety of service options in order to give your home a much-needed boost and get things back up and running. Established in 1962, you can count on our expertise and experience when it comes to all your home comfort needs – and you will always get the satisfaction that you deserve. Read through some of the reviews below to discover just how many lives have been improved by this quality service!
Air Conditioning Repair in Corinth, TX
Every homeowner will eventually need AC repair someday. After all, your AC unit is just a machine, and on top of that, we all know how summertime can be in Texas… Sun, sun, and more sun!
Imagine this: you return home after a full working day and all you want is to chill out and refresh yourself. You turn on your air conditioning unit and it simply doesn’t work. Even if you want to leave it for the next day, there is no way you can stand the heat. It is time to call for an emergency AC repair.
Comfort Experts is your fastest and most reliable solution when it comes to AC services. We are happy to offer you AC services in your Corinth home.
Comforts Experts Means Professional AC Services in Corinth
If you need AC services in Corinth, TX, look no further than our team. With Comfort Experts Inc., all the hassle is taken away from you. We provide professional service and are happy to take on any projects regarding AC services to help you be as comfortable as possible in your home.
Call us now to take advantage of our fast and reliable service. We will come to your home and take a professional look at all problems you may have and give you our best opinion about all the issues your air conditioning unit is facing. We also are happy to provide free second opinions on another air conditioner quote.
A Company You Can Trust
Have you ever considered that your power bills may be much higher because of your HVAC’s performance? In fact, the first sign your AC unit is not performing the way it should actually be your last electric bills and the overall air quality of your house.
Don’t worry, help is on the way. Now all Corinth residents can rely on our exceptional and dedicated team not only for your AC service but also for the maintenance of your equipment as well. With our maintenance agreement, you will have less to worry about with your AC units because we’ll be keeping an eye on them regularly.
Additionally, we will inspect your entire home in order to improve the overall quality of air. We will closely look at your central air unit to help prevent any issues in the future. Not only will we help you prevent a costly and often avoidable repair, but we will also help you reduce your electric bill and improve the overall air quality of your house.
for Corinth, TX
Our Reviews by City
Great service, as always
Hector - Corinth, TX 76210
Blake came and troubleshot my misbehaving HVAC. How found the issues and provided options to resolve it quickly, and was spot on with his diagnosis. While it wasn’t the best news to get right around the holidays, at least I know what’s up with the unit and have a plan of attack. I always get great service from Comfort Experts and their technicians like Blake are professional and courteous.
Sandi - Corinth, TX 76210
Very Knowledgeable, friendly, and polite. On- time, and completed job in a timely manner. Offered different options and informed me of service packages. Happy with service. Thank you for getting us cool again!
Jon - Corinth, TX 76210
Technician was very thorough and detailed.
Excellent Service, Great Delivery
Hector - Corinth, TX 76210
2nd unit purchased this year and another quick and professional delivery. Ensured everything was up to code and went the extra mile to ensure they met requirements. 1st unit purchased had an issue they resolved asap and under warranty and expecting the same with this unit. Great communication and ensured any questions I had were answered right away. Gave instructions for care (unit is more maintenance-free than the older unit) and ensured my Nest unit was configured properly. Hauled away old unit and ensured everything was clean before leaving. Overall, very pleased with the process, and while, yeah, it's not cheap, at least I won't have to worry about these units for another decade or so.
Trish - Corinth, TX 76210
Hector - Corinth, TX 76210
Mark was friendly, knowledgeable and provided a very thorough review of plumbing in my home. I was very happy to have him come in and discuss what he encountered, as part of my contract, including what could be life-saving recommendations for rusty gas connections. One more reason I enjoy working with Comfort Experts!
Edith - Corinth, TX 76210
Did an Awesome job. Professional and politeness.
Thorough and amazing price!
Trish - Corinth, TX 76210
Sandra - Corinth, TX 76210
William - Corinth, TX 76210
Dennis good, situation bad
Response from Comfort Experts Inc.:
Thank you for bringing this to our attention- we are sorry to hear of the level of service you received. We will dig deeper into why this happened so that we can do better in the future.
Blair - Corinth, TX 76210
Jordan was curteous and friendly while helping us out today and I thank you guys so much for his help
Excellent customer service
Teresa - Corinth, TX 76208
Tech was great
William - Corinth, TX 76210
Was not informed about delay in arrival arrived at 8, left at midnight Dispatch did not keep me informed Tech was great(5 stars)
Tech arrived at a 2 system tune-up. Upon inspection, the capacitors were within specs. The condenser coils were clean. The systems did not appear to have surge protection. The filters were a little dirty. The ductwork was dirty. The drains were clear and treatment strips were added per customer request. There was evidence of previous water issues upstairs. The heating systems reached complete ignition. The systems were functioning upon departure.
11/20/23 Tyler - AO Smith sent in new burner unit and control valve for water heater. Installed both and also installed a drip line for the gas line so it's up to code.
On this job I replaced filters tested both side of each ssytem and cleaned condensers. These systems are less then 2 years old and operate vary well. I recommend replacing the uv systems with longer lasting and stronger iAQ 200.
Install dual fuel 24k horizontal with high efficiency filtration and duct cleaning
Tech arrived at a membership service call. Upon inspection, the furnace was giving codes for limit switch. The system was reset and reached complete ignition however the blower motor did not come on. The capacitor was tested and out of tolerance. The motor was emanating heat. The ignition components were scorched. The inducer motor was pulling very high amperage. The coil and blower area was dirty. The customer was informed of recommendations today. Due to age, condition, presence of R22 and price of repairs; it is recommended that the customer speak with a Comfort Advisor about upgrading to something more reliable with warranties behind it. The customer agreed and the meeting is set for Friday afternoon 3-5.
Heating tune up on both systems went smoothly both systems have new filters and both kick in to heating and heat properly.
09/16/23 cleared blockage in Upstairs lav drain and then installed new customer supplied sink faucet. PLEASE send invoice as two separate parts $184.10
Tech arrived at a 2022 AirEase inverter board tuneup. Upon inspection the contactor was in working condition. The board showed no errors. The system had surge protection. The condenser coils were hosed off to assist with air flow across the coils. The filter was dirty. There was a damaged duct that was taped. The blower area was a little dirty. The drain was clear and vinegar was poured. The water heater was evaluated there was rust and corrosion on the tank and fittings. The customer has another water heater that is ready for install. Mark was contacted and the customer was given a quote for replacement. The customer will hold off right now but my call back later in the year. The system was functioning upon departure.
No issues detected. Refrigerant levels are normal. Washed and cleaned both outdoor units. Changed filters. Recommend compressor saver for efficiency and longevity
Low voltage issue on the reversing valve re attached it and the system worked as intended.
Upon arrival found float switch activation Drain system improperly installed and is not allowing system drain properly recommended to cust wenget it fixed so we do not continue to have this problem Drain cleared Drain treatment installed New titanium memb
2012 Goodman Gas Furnace Electrical connections were acceptable Blower capacitor wasoutof manufacturer range , customer made a great choice and replaced. Evaporator coil was acceptable Drain was clear and draining poured agallon of water down 2012 Goodman Straight Cool Dual Capacitor wad out of manufacturer range, customer made a great choice in replacement Refrigerant levels were acceptable at this time Washed the unit from the inside out Waxed thetip of the unit Condenser Fan was acceptable
Upon arrival to customers house system was cooling During my inspection I confirmed the units were operating as they should and refrigerant charge on the system were good Left customers house with system cooling
Upon arrival for service system off. Inspected system and found drain line clogged at p trap and p trap connection failed. Cleared line and repaired connection. Reset p trap and tested with 2 Gallons of water. Tried to get in contact with customer to collect payment. Could not reach customer as they are out of country. Customer returns tomorrow, son requested we call them tomorrow to collect payment.
#iaq upon arrival for tune up system on and cooling. Inspected outdoor unit. Fan and compressor amp draw within unit specifications. Capacitor within tolerance. Refrigerant pressure good. Cleaned unit. Inspected indoor unit. Blowers and coils clean. Drain line clear. Defrost functioning. Recommended adding compressor saver kit to reduce wear and extend life of compressor. Left system on and cooling.
Arrived at location and spoke with home owner. Inspected indoor unit. Electrical connections tight. Excessive dust buildup in supply duct. Recommended duct cleaning and blower pull and clean. Home owner interested in duct cleaning, may contact office in near future to schedule. Blower capacitor in spec. Temperature delta within acceptable range. Filter changed. Coil clean and in good condition. Inspected outdoor unit. Electrical connections tight. Fan and compressor Amp draw good. Refrigerant levels good. Capacitor in spec. Fan motor housing rusting. Coil washed. Coil in good condition. Surge protection not active. Recommended replacement, home owner agreed.
Tune up showed an extremely drity return I recommed a duct cleaning and a uv light to maintain a healthy system. Other wise system is new and works great.
Checked inside and systems. Downstairs system is well. Amp draws and capacitor readings are within range. Blower and coil are clean. Ducts are clean. Upstairs unit amp draws and capacitor tolerances are within range, start up amp draw is higher than max. Blower and coil is clean ducts are clean. Talked to customer about surge protection and hard start kits. Systems left in working order, changed thermostat batteries
#iaq upon arrival for tune up on 3 year old diakan gas furnace system it was on and heating. Inspected outdoor unit. Unit is inverter board. Inverter board has no hot spots. power draw on system good. Cleaned unit. Refrigerant pressure good. Inspected indoor unit. Blower has slight dust buildup. Coil clean. Furnace ignited and heated properly. Drain line clear. Recommended whole home surge protector for protection of home. Left system on and heating.
Tech arrived for a cooling tune-up*2. It was cold and rainy. There was a ride along employee present. Upstairs system- the capacitor was within specs. The contactor was in working condition. The condenser coils were dirty and were hosed off to assist with air flow across the coils. There was no observed surge protection. The filter was dirty and replaced. The ductwork was dirty. The drain was clear and bleach was poured. The Delta was 19 degrees. Downstairs system- the capacitor was within specs. The contactor was in working condition. The contactor was audibly buzzing. The condenser coils were dirty and were hosed off to assist with air flow. There was no observed surge protection. The filter was dirty and was replaced. The drain system was clear and bleach was poured. The Delta was 21 degrees. The customer was informed of recommendations. The customer decided to move forward with preventative maintenance including contactor replacement for the downstairs system and drain treatme
Tech arrived at a 1st year tuneup. The capacitor was within specs. The contactor was in working condition. The condenser coils were extremely dirty and were hosed off to assist with air flow across the coils. There were 2 filters on the system. The one at the attic unit was removed. The Delta was within range. The drain was clear. The blower area was a little dirty. There was no observed surge protection. The water heater was evaluated. The system appeared to be a 2008 model. There was no pan beneath the heater and there was corrosion on the fittings. Customer was informed of the recommendations and was given quotes. The customer decided not to move forward today. The customer was informed that a laps in membership may result in the loss of labor warranties. The system was functioning upon departure.
Downstairs: 2 year old Amana gas system, duct cleaning, system is operating normally at this time. Replaced filter provided. Upstairs: 3 year old Amana gas system, duct cleaning. System is operating normally at this time. Water heater. Calling home Warranty company
Found some debris lodged inside of the inducer motor. After clearing the debris, the furnace fired right up.
Tech arrived for a HTU on the Upstairs system. <br> The capacitor was within specs. The contactor was in working condition. The Delta was within range. The filter was a little dirty. There was no replacement today. The customer was given order information. The drain was clear and bleach was poured. The heating system reached complete ignition. The systems did not appear to have Surge Protection. <br> <br> The customer decided to move forward with surge protection today. Surge Protectors were added to both systems. The items were installed, tested, and functioning.<br> <br> The system was functioning upon departure.
Install Dual fuel 24k horizontal upstairs with high efficiency filtration, whip, disconnect and drain pan