Comfort Experts promises customer service that exceeds the expectations of Hudson Oaks TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Hudson Oaks TX.
Had a stubborn Problem..lol Wyatt and his partner in crime… Stuck with it! Found the leak! Fixed the problem!
Joel was on time, easy to explain what he was doing & what he found. Nice young man👍😉.
Mark was very polite, timely & thorough!
Professional,friendly, and knowledgeable
Mark was quick at completing the annual maintenance check of the system and gave me an overall feel for the condition of the unit.
Wyatt was very courteous & knowledgeable, and explained everything he found & did, to us (no trouble found-all was working fine😉). Thank you👍😉. The Solt family
Alex performed good, comprehensive service when our newly installed heat pump stopped working.
The braze had come loose and leaked the refrigerant out tripping the limit switch fixed the hole and pressure tested , pulled a vacuum and refilled unit. Left it in cooling
Did a Cooling Tune-up on 10 year old Amana heat pump, tested capacitor, checked filter, drain is good, recommended replacing system due to age, upgrade to IAQ200,coil clean and blower wheel cleaning, refrigerant levels are good, customer verified unit was working properly when leaving
Two Trane heat pumps with air handlers in stalled in 2021. All electrical connections are tight with no corrosion. Both ECM blower motors are acceptable. Both blower wheels are clean. Both evap coils are clean. condensing unit capacitors and contactors are acceptable. Both compressors and condenser fan motors are acceptable. Refrigerant and air flow levels are acceptable.
2018 Goodman Air Handler and Heat Pump CTU heating elements were functional and within manufacturer range Blower motor and wheel were acceptable Blower capacitor was within manufacturer range Evaporator coil was acceptable Drain was clear and draining poured a gallon of water down Changed the filter for customer Electrical connections were acceptable Outdoor low on refrigerant, bad accumulator ordered under p&l warr
American standard heat pump with air handler installed in 2019. All electrical connections are tight with no corrosion. X13 blower motor is acceptable. Blower wheel and evap coil are clean. 70/5 dual run capacitor and contactor are in range. Condenser fan motor and compressor are acceptable. Refrigerant levels and air flow are acceptable.
32x74 pan needs replacement. Blocked drain and non functional drain switch caused water to leak onto ceiling. Cleared drain, added slow release drain treatment and installed functioning drain switch. Customer would like a receipt emailed to him.
Customer needs to share estimates with the trust who owns the home. Rheem heat pump with air handler installed in 2020. All electrical connections are tight with no corrosion. Heat strips are in range. Blower wheel and evap coil are clean. Drain switch is faulty and customer needs new one. Dual run capacitor and contactor are acceptable. Compressor is acceptable but condenser fan motor is leaking oil and will fail. Refrigerant levels and airflow are acceptable. Estimates have been sent to customer via email so he can get approval from the trust.
Did a evaluation on 2 year old Amana system, checked capacitor, checked filter, drain is good,found wire to contactor for the heat strips melted and broke off so system wasn't getting power,replace contactor and fix the wire and got system operating correctly B
Did a evaluation on 2 year old Carrier system, checked capacitor, checked filter, drain is good, found evaporator coil froze up,trued to run heat to defrost coil and found blower motor was not running,checked blower motor by sending 24v to it and did not turn on,checked control board and found it was not sending 24v to the blower motor,recommended a membership, blower motor, and control board for furnace Picture of motor data tag in form Customer wants us to get price for blower motor
Level 1 48k gas Code items Permits 1st year copper $2500 down by CC Installing on 11/21/22
Call (817) 341-5149 or Message