Comfort Experts promises customer service that exceeds the expectations of Hudson Oaks TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Hudson Oaks TX.
Mark was quick at completing the annual maintenance check of the system and gave me an overall feel for the condition of the unit.
Wyatt was very courteous & knowledgeable, and explained everything he found & did, to us (no trouble found-all was working fine😉). Thank you👍😉. The Solt family
Alex performed good, comprehensive service when our newly installed heat pump stopped working.
My opinion he should get a raise. Joel was awesome. So grateful for his help today!
Good experience with Dennis !
My husband and I lack the experience and knowledge, to understand the complexity and failure of our air conditioning system: What we can share, is that upon Joel’s arrival, our AC units were not adequately cooling our home, but after Joel’s service call, our home was pleasantly cooling! He was thorough and informative. Due to no fault of his own, We can’t repeat a word he shared, regarding our problem. But, we have his contact information (JB) in our iPhones (under Favorites). Joel (JB) is an extraordinary Service Technician!
Level 1 48k gas Code items Permits 1st year copper $2500 down by CC Installing on 11/21/22
Thoroughly inspected the 22 year old gas furnace, squirrel cage fell off motor damaging cage/motor, system R22, heat exchanger has hot spots, no drain safety and the system’s gas line is out of code.
2019 Carrier Air Handler Drain was clear and draining poured a gallon of water down Evaporator coil was acceptable Filter was clean Delta T was acceptable 19.3° Heating elements were functional and within manufacturer range Blower motor and wheel were acceptable Electrical Connections were acceptable 2019 Carrier Heat Pump Dual capacitor is 70/7.5 +-6% it's reading at 68/7.05 it's getting close to being out of range on fan side. Recommend replacing Fan blades and motor were acceptable Primary electrical contactor was acceptable Fan and compressor amps were acceptable Washed the unit from inside out Waxed the top of the unit
Carrier heat pump with air handler installed in 2017. All electrical connections are tight. Biological growth in blower chamber and on blower wheel. X13 blower motor is strong. Heat strips are in range. 70/7.5 dual run capacitor is bad and needs to be replaced. Reversing valve and defrost control board are functioning as they should. Refrigerant and airflow levels are satisfactory. Customer refused repairs.
2017 Trane Air Handler Blower wheel and motor were acceptable Filter was just changed by customer Delta T of 18 Evaporator coil was acceptable Heating elements were functional and within manufacturer range Drain was clear and draining poured a gallon of water down Electrical connections were acceptable 2017 Trane Heat Pump Dual capacitor was within manufacturer range Refrigerant levels were acceptable Fan blades and motor were acceptable Washed the unit from inside out Waxed the top of the unit Cleaned the debree out of the unit
STU complete Drain line clear Filter replaced in Oct 22 per customer Evaporator coil inspected Blower wheel inspected Heatstrips inspected Electrical connections acceptable Outdoor Coils washed Debris removed from inside Capacitor acceptable 35/5 Electrical connections acceptable Refrigerant acceptable Emailed estimates per customer request.
Did a AHC on 2 9 year old Trane systems, checked capacitors, changed filters,flushed drains, recommended a membership, drain switch, compressor saver, and blower wheel cleaning,refrigerant levels are good, customer verified unit was working properly when leaving
Install 18K Heat Pump Mini split
Performed ahc, 2 year old gas horizontal comfort maker, cleaned condenser, drains clear, flame sensor heavy corrosion, no drain protection installed. No service to collect service fee, office to call and collect.
Upon arrival for the 1962 special, I found a second system that we added to the visit. Sat down with Mrs.Lixey and discussed options, she deferred to her Husband which was at work. I emailed estimates to husband but have not spoken to him yet. I would like to set up a follow-up call on Thursday. Both condenser units had faulty 70/5 capacitors Both units were Carrier 2014.