Comfort Experts promises customer service that exceeds the expectations of Graford TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Graford TX.
Did a evaluation on system, unit was not running when i arrived, checked capacitor and found dual run capacitor was opened, talked to customer and they wanted to replace the capacitor, replaced the capacitor and got unit running properly, drain is good, checked filter,refrigerant levels are good, customer verified unit was working properly when leaving, customer got a copper membership B
Reset low pressure switch on arrival. Removed dirty filter and inspected system. Found dirty coil and failing condenser fan motor. Located clogged primary drain. Replaced condenser fan motor and cleaned outdoor coil. Cleared primary drain line
6/24/22 Mark W - arrived evaluated project the original quote is not accurate. Mark will check material needed and verify with management the correct cost of completing this project. By customer request he wants to feed off of a light to install the ceiling fan in the back of house
Customer called and said upstairs unit was not cooling properly. When I arrived upstairs was 78Â° I went up in the attic and found that the blower motor was not coming on. After doing my test I deduced that it was a bad motor as I was getting power to the circuitboard and it was clicking like it wanted to come on but it was still not coming on. I am waiting on a price and availability check on the new Ecm motor.
Cleaned and inspected system. Replaced filter but filter was undersized. Recommended customer purchase correct filter. Found no trap on primary drain. Recommend adding trap and primary drain switch
Changed filter media and inspected system. Misc. Dual cap 45/5
Inside ducts are dusty, outside unit dual cap is reading low, customer choose for me to replace dual cap.
Performed super tune up, thoroughly inspected all the components, showed the customer what filter they need, and washed the condenser coil. Replaced the UV Germicidal Sanitizing System due to bad ballast, and primary electrical control unit due to having burned and pitted contact points. System is functioning properly, left on in heating.