Comfort Experts promises customer service that exceeds the expectations of Graford TX residents.
Call us now at:(817) 341-5149. We’d love the opportunity to earn your business as we have with your neighbors in Graford TX.
Add extensions to fan
Was having trouble with thermostat, set system to heat and it is operating normally.
Arrived and performed plumbing tune up. Everything looked to be in working condition and everything has been updated
2016 Coleman Air Handler Blower wheel and motor were acceptable Evaporator coil was acceptable Checked filter for customer did not need to be changed yet Poured a gallon of water down the drain and it was clear and draining Delta T was acceptable 22.8° Electrical Connections were acceptable UV light was functional had been changed in 2021 Heating elements were acceptable 2016 Coleman Heat Pump Fan blades and motor were acceptable Cleaned out the debree out of the unit Washed the unit from inside out Waxed the top of the unit Dual Capacitor was within manufacturer range Refrigerant levels were acceptable
All 3 bathroom toilet needs the seats tightened 1/2 bath and main bath needs faucets tightened Master bath needs stopper put back in on left sink Right sink faucet doesn’t have a stop on hot water handle The dishwasher has been removed and drain is not terminated properly Tighten two faucet and tighten all three toilet seats put stopper in sink in master bathroom on right side Next time we come out we need to bring a 3/4 rubber plug for garbage disposal
Did a evaluation on system, unit was not running when i arrived, checked capacitor and found dual run capacitor was opened, talked to customer and they wanted to replace the capacitor, replaced the capacitor and got unit running properly, drain is good, checked filter,refrigerant levels are good, customer verified unit was working properly when leaving, customer got a copper membership B
Reset low pressure switch on arrival. Removed dirty filter and inspected system. Found dirty coil and failing condenser fan motor. Located clogged primary drain. Replaced condenser fan motor and cleaned outdoor coil. Cleared primary drain line
6/24/22 Mark W - arrived evaluated project the original quote is not accurate. Mark will check material needed and verify with management the correct cost of completing this project. By customer request he wants to feed off of a light to install the ceiling fan in the back of house
Customer called and said upstairs unit was not cooling properly. When I arrived upstairs was 78Â° I went up in the attic and found that the blower motor was not coming on. After doing my test I deduced that it was a bad motor as I was getting power to the circuitboard and it was clicking like it wanted to come on but it was still not coming on. I am waiting on a price and availability check on the new Ecm motor.
Call (817) 341-5149 or Message