Sachse AC & Heating Services
The purpose of your heating, air conditioning and ventilation system is to provide a comfortable and safe environment inside your home. This could be anything from keeping your home heated or cooled at your preferred temperature to improving the indoor air quality and circulation of your home to help fight against respiratory and other illnesses. Can you guarantee that your unit is running at its full potential and successfully providing the ideal comfort and safety for your Sachse home? If you answer “no” to this question it is time to have your unit inspected. Call us today at 817-341-5149 to schedule your inspection!
Sachse AC Repair & Replacement
If your unit is unable to be repaired and has to be replaced, we’re here to quickly get a new unit put in so you can get back to the comfort you deserve. All you have to do is choose a new system! We provide a wide range of HVAC units to choose from so we know that you will be able to find a new system that caters to your needs.
Our 5-star online reviews show that we are dedicated to customer satisfaction. We have made it our goal to leave you saying that you had a good experience with our company. We take pride in the work we do and always back our work with a 100% customer satisfaction guarantee. You will always be left satisfied and we will always leave knowing we have successfully assisted your family with your Sachse AC repair needs.
Here For All Your HVAC Needs
Comfort Experts, Inc. has made it our mission to keep Sachse families comfortable all year long and assure that your home is a safe environment. No matter the issue with your heating and cooling systems, we’re here to help. By offering AC inspection and repair, we can diagnose a malfunction quickly and fix the problem, returning your system to peak performance.
In addition to heating and cooling, we specialize in plumbing and electrical services so you don’t have to worry about hunting down multiple contractors. We take care of all your HVAC systems from start to finish. For the most comfortable call you’ll ever make, we’ll be here 24/7 at 817-341-5149 !
for Sachse, TX
Our Reviews by City
Upon arrival systems were in working condition. Looking at the indoor units all electrical connections and components are good. Blower and coils are clean. Drain lines are clear and flowing. Recommended pan strips customer agreed. Looking at the outdoor units all electrical connections and components are good. Capacitors are within tolerance. Amp draws are acceptable. Upstairs unit had compressor saver, but downstairs didn't , recommended we put one on and customer agreed. Left both systems in working condition. Thank you for choosing comfort experts.
Performed a tune up on system. Poured 1 gallon of water through drain and water drained normally. Did find that unit did not have any water safety installed. Tested pressures and amp draws on outdoor unit and all were good. Tested capacitor and found capacitor to be dead. Previous company had installed a supco hard start on unit and hard start was giving high readings. Cleaned off outdoor coil inside and out. Recommended to customer that drain switch and/or a new capacitor would be needed. Found no other issues at this time.
Tech arrived at a warranty service call. Upon inspection, the 35mfd capacitor was out of tolerance and was replaced with a 35/5 capacitor. The capacitor was different than the one it was replaced and wiring adjustments were made. The UV system wete not working and the bulbs were expired. These bulbs were replaced today. #solar The system was functioning upon departure.
Upon arrival for tune up systems on and cooling. Inspected outdoor units. Fan and compressor amp draws within unit specifications. Refrigerant pressures good. Downstairs capacitor within tolerance. Upstairs capacitor out of tolerance. Inspected indoor units. Blower have dust buildup. Coils clean. Drain lines clear. Recommended replacement of capacitor. Left systems on and cooling.
Tech arrived for a service call 45. Upon inspection there were only 2 heat strips functioning. Wires were moved and all strips regained functionality. The drain line connection to the pan failed during the call. A new drain pan is being ordered and will be replaced at a later date. The cooling was disconnected at this time. Holding for parts. Heating was functioning upon departure.
Completed duct cleaning
Tech arrived for a STU*2. Upon inspection the capacitora were within specs. The contactorless boards were indicating normal cooling. The upstairs system surge protector was functioning. The downstairs system surge protector was not functioning. This item was replaced and functioning. The filters were very dirty and were replaced. The ducts were also dirty. The blower area were clean. The UV systems were functioning. The drains were clear and bleach was poured. The heating systems were functioning. The customer decided to move forward with 2 level 1 duct cleanings today. Thecleanings are set for Tues Dec 13th afternoon.
Tech arrived for a CTU*2. Upon arrival there was a real estate sign out front. The house was not currently under contract and the normal tuneup fee was left in place. The customer mentioned that the home inspector noticed possible problem with the filter box, drain lines, and delta. Normal maintenance tuneups were conducted today. The downstairs system- The capacitor and contactor were within specs. The compressor and condenser fan motor amps were high. The condenser fan motor was rusted and labored. The refrigerant and delta were at acceptable levels. The system was a little dirty. A duct cleaning is recommended. The customer was informed of the benefits behind adding a Compressor Saver. The upstairs system- The capacitor and contactor were within specs. The amp draws were at acceptable levels. The delay was with in range at 17 degrees. Drain system were clear and bleach was poured. Tape was added around the filter access. Both systems were functioning upon departure.
Arrived for NC call. Unit showing open start circuit lockout error code Capacitor testing at 0. Replaced per PL. drain took a quart of water no problem Capacitor replacement now system is running
Completed repair. Unit giving start circuit lockout error code. Compressor capacitor dead. Replaced capacitor and cleared error code. Unit running in cooling on departure